Air  Humidifying by Adding Steam or Water
Air can be humidified by adding water or steam.
Air can be humidified by
 adding water, or
 adding water vapor  or steam
Humidifying Air by adding Water
If water is added to the air without any heat supply the state of the air changes adiabatic along a constant enthalpy line  h  in the Mollier or psychrometric chart . The dry temperature of the air decreases as indicated in the process from A to C in the Mollier diagram above.
The amount of water required to change the specific humidity can be calculated as
m _{ w } = v ρ (x _{ C }  x _{ A } ) (1)
where
m _{ w } = mass of added water (kg/s)
v = volume air flow (m ^{ 3 } /s)
ρ = density of air (kg/m ^{ 3 } )  varies with temperature, 1.204 kg/m ^{ 3 } at 20 ^{ o } C and 1 atm
x = humidity ratio (kg _{ h2o } /kg _{ dry_air } )
If water is added at the same temperature as the air the enthalpy change is zero.
Example  Humidifying Air by adding Water
An airflow of 3000 m ^{ 3 } /h at 25 ^{ o } C and 10% relative humidity (A) is humidified to 60% relative humidity (C) by adding water through spray nozzles.
Using the Mollier diagram following the constant enthalpy line 30 kJ/kg from A to 60% relative humidity, the state at C can be found at 14.7 ^{ o } C .
The humidity ratio at (A) is 0.002 kg/kg and at (C) 0.0062 kg/kg .
The amount of water:
m _{ w } = ((3000 m ^{ 3 } /h) / (3600 s/h)) (1.184 kg/m ^{ 3 } ) ( (0.0062 kg/kg)  (0.002 kg/kg) )
= 0.0041 kg/s
= 14.9 kg/h
Humidifying Air by adding Steam
If steam is added to the air the state will change along a constant dh/dx  line for steam as indicated in process A to B in the Mollier diagram above.
When adding saturated steam at atmospheric pressure the constant line dh/dx = 2502 kJ/kg (the evaporation heat of water at atmospheric pressure). When adding saturated steam at atmospheric pressure the temperature rise is very small  in general less than 1 ^{ o } C . For practical purposes the process of adding saturated steam at atmospheric pressure approximates the horizontal temperature line.
The water vapor added can be calculated using (1).
The enthalpy added can be estimated by using the Mollier diagram or a psyhrometric chart.
Example  Humidifying Air by adding Steam
An airflow of 3000 m ^{ 3 } /h at 25 ^{ o } C and 10% relative humidity (A) is humidified to 60% relative humidity (B) by adding saturated steam at atmospheric pressure.
Using the Mollier diagram the process from (A) to (B) can be approximated by following the constant temperature line 25 ^{ o } C to 60% relative humidity and approximately 25.5 ^{ o } C (a temperature increase less than 1 ^{ o } C ).
Note!  by adding enough steam the state of air (B) is moved to the saturation line where the air is fully saturated. By adding even more steam the process starts following the saturation line  moisture content and dry bulb temperature will increase  and droplets or fog may be introduced in the moist air.
The humidity ratio at (A) is 0.002 kg/kg and at (B) 0.012 kg/kg .
The amount of water added can be calculated as:
m _{ w } = ((3000 m ^{ 3 } /h) / (3600 s/h)) (1.184 kg/m ^{ 3 } ) ( (0.012 kg/kg)  (0.002 kg/kg) )
= 0.01 kg/s
= 35.5 kg/h
The enthalpy change can be estimated from the Mollier diagram. The enthaply at (A) is 30 kJ/kg and at (B) 55 kJ/kg . The enthalpy difference is
dh = (55 kJ/kg)  (30 kJ/kg)
= 25 kJ/kg
The total heat added by the steam can be calculated as:
q = ((3000 m ^{ 3 } /h) / (3600 s/h)) (1.184 kg/m ^{ 3 } ) (55 kJ/kg  30 kJ/kg)
= 24.7 (kJ/s, kW)
Example  Humidifying Air with Steam in the Psychrometric Chart
The chart below indicates a similar process of humidifying air with steam in the psychrometric chart.
Steam Required for Humidification at different Outdoor Temperatures
Steam required for humidification of indoor space at 21°C (70°F), 2 airchanges per hour and 70% outdoor relative humidity:
Related Topics

Air Psychrometrics
Moist and humid air  psychrometric charts, Mollier diagrams, aircondition temperatures and absolute and relative humidity and moisture content.
Related Documents

Air  Absolute Humidity
Absolute humidity is the actual mass of water vapor present in the air water vapor mixture. 
Air  Density, Specific Weight and Thermal Expansion Coefficient vs. Temperature and Pressure
Online calculator, figures and tables showing density, specific weight and thermal expansion coefficients of air at temperatures ranging 100 to 1600 °C (140 to 2900 °F) at atmospheric and higher pressure  Imperial and SI Units. 
Air  Heating, Cooling, Mixing, Humidifying or Dehumidifying Processes
Basic air changing state processes  heating, cooling, mixing, humidifying and dehumidifying by adding steam or water  psychometric diagrams and the Mollier charts. 
Air  Humidifying with Steam  Imperial Units
Estimate the amount of steam required (lb/h in 100 cfm) in humid air. 
Air  Humidifying with Steam, SI units
Using steam to humidify air. 
Air  Moisture Holding Capacity vs. Temperature
The moisture holding capacity of air increases with temperature. 
Air  Psychrometric Chart for Standard Atmospheric Conditions  Imperial Units
Psychrometric chart for air at barometric pressure 29.921 inches of Mercury and temperature ranging 20^{o}F to 120^{o}F. 
Air and Steam Mixtures
Air in the steam will lower the surface temperatures in heat exchangers  and less heat will be transferred. 
Cooling and Heating Equations
Latent and sensible cooling and heating equations  imperial units. 
Heat Recovery Efficiency
Classification of heat recovery efficiencies  temperature efficiency, moisture efficiency and enthalpy efficiency  online heat exchanger efficiency calculator. 
Humidifiers
Sprayed coils, spinning discs and steam humidifiers. 
Mixing of Humid Air
The change in state wwhen mixing moist air  enthalpy, heat, temperature and specific humidity. 
Moist Air  Cooling and Dehumidifying
Cooling and dehumidifying processes of moist and humid air  sensible and latent cooling. 
Moist Air  Density vs. Water Content and Temperature
Density of the mix of dry air and water vapor  moist humid air. 
Moist Air  Enthalpy
Sensible and latent heat of moist air. 
Moist Air  the Mollier Diagram
The Mollier diagram is a graphic representation of the relationship between air temperature, moisture content and enthalpy  and is a basic design tool for building engineers and designers. 
Moist Air  Transforming the Mollier Diagram to a Psychrometric Chart  or vice versa
The relationship between the psycrometric chart and the Mollier diagram. 
Steam Heating Air
Calculate steam heated air systems. 
Steam Heating Processes  Load Calculating
Calculating the amount of steam in nonflow batch and continuous flow heating processes. 
Vapor and Steam
An introduction to vapor and steam. 
Wet Steam  Enthalpy
Wet steam, dryness fraction and enthalpy.