Moist Air  Enthalpy
Sensible and latent heat of moist air.
Moist air is a mixture of dry air and water vapor. In atmospheric air water vapor content varies from 0  3% by mass. The enthalpy of moist and humid air includes the
 enthalpy of the dry air  the sensible heat
 enthalpy of the evaporated water in the air  the latent heat
The total enthalpy  sensible and latent  is used when calculating cooling and heating processes.
Specific enthalpy  h  (J/kg, Btu/lb) of moist air is defined as the total enthalpy (J, Btu) of the dry air and the water vapor mixture  per unit mass (kg, lb) of dry air.
Specific Enthalpy of Moist Air
Specific enthalpy of moist air can be expressed as:
h = h_{a} + x h_{w} (1)
where
h= specific enthalpy of moist air (kJ/kg, Btu/lb)
h_{a}= specific enthalpy of dry air (kJ/kg, Btu/lb)
x= humidity ratio (kg/kg, lb/lb)
h_{w}= specific enthalpy of water vapor (kJ/kg, Btu/lb)
Specific Enthalpy of Dry Air  the Sensible Heat
Assuming constant pressure conditions the specific enthalpy of dry air can be expressed as:
h_{a} = c_{pa} t (2)
where
c_{pa}= specific heat of air at constant pressure (kJ/kg^{o}C, kWs/kgK, Btu/lb^{o}F)
t= air temperature (^{o}C, ^{o}F)
For air temperature between 100^{o}C(150^{o}F) and 100^{o}C(212^{o}F) the specific heat can be set to
c_{pa}= 1.006 (kJ/kg^{o}C)
= 0.240 (Btu/lb^{o}F)
Note!  that the enthalpy is 0 kJ/kg at 0^{o}C. This is not correct according the definition of enthalpy in the thermodynamics, but for practical purposes in air psychrometrics this assumption is good enough since our interest is the enthalpy difference.
Specific Enthalpy of Water Vapor  the Latent Heat
Assuming constant pressure conditions the specific enthalpy of water vapor can be expressed as:
h_{w} = c_{pw} t + h_{we} (3)
where
c_{pw}= specific heat of water vapor at constant pressure (kJ/kg^{o}C, kWs/kgK)
t= water vapor temperature (^{o}C)
h_{we}= evaporation heat of water at 0^{o}C (kJ/kg)
For water vapor the specific heat can be set to
c_{pw}= 1.86 (kJ/kg^{o}C)
= 0.444 (Btu/lb^{o}F)
The evaporation heat (water at 0^{o}C, 32^{o}F) can be set to
h_{we}= 2501 (kJ/kg)
= 1075 (Btu/lb)
Using (2) and (3), (1) can be modified to
h = c_{pa} t + x [c_{pw} t + h_{we}] (4)
(1b) in metric units
h = (1.006 kJ/kg^{o}C) t + x [(1.86 kJ/kg^{o}C) t + (2501 kJ/kg)] (5)
where
h = enthalpy (kJ/kg)
x = mass of water vapor (kg/kg)
t = temperature (^{o}C)
(1b) in Imperial units
h = (0.240 Btu/lb^{o}F) t + x [(0.444 Btu/lb^{o}F) t + (1075 Btu/lb)] (6)
where
h = enthalpy (Btu/lb)
x = mass of water vapor (lb/lb)
t = temperature (^{o}F)
Note!  the "reference" points for the metric and imperial enthalpies are different.
 for eq. (5) metric units  the "reference" point for enthalpy h = 0 (kJ/kg) is t = 0 ^{o}C(32^{o}F) and x = 0 kg/kg
 for eq. (6) imperial units  the "reference" point for enthalpy h = 0 (Btu/lb) is t = 0 ^{o}F(17.8^{o}C) and x = 0 lb/lb. The evaporation heat for water at 0 ^{o}F is 1061 Btu/lb as used in eq. (6).
You can not convert from metric to imperial enthalpy or vice versa directly.
Example  Enthalpy in Moist Air
The enthalpy of humid air at 25^{o}C with specific moisture content x = 0.0203 kg/kg (saturation), can be calculated as:
h =(1.006 kJ/kg^{o}C) (25^{o}C) + (0.0203 kg/kg) [(1.86 kJ/kg^{o}C) (25^{o}C) + (2501 kJ/kg)]
= (25.15 kJ/kg) + [(0.94 kJ/kg) + (50.77 kJ/kg)]
= 76.9 (kJ/kg)
Note!  the latent heat due to evaporation of water is the major part of the enthalpy. The sensible heat due to heating evaporated water vapor can be almost neglected.
Enthalpy of Moist Air containing Water as Fog
If the air contains more water than limited by saturation, some of the water exists as droplets  as fog. The enthalpy of moist air with fog can be expressed as:
h = c_{pa} t + x_{s} [c_{pw} t + h_{we}] + (x  x_{s}) c_{w}t (7)
where
x_{s}= humidity ratio at saturation (kg/kg)
c_{w}= 4.19  specific heat water (kJ/kg^{o}C)
Enthalpy of Moist Air containing Ice or Snow
If the air contains water as ice or snow, the enthalpy of air can be expressed as:
h = c_{pa} t + x_{s} [c_{pw} t + h_{we}] + (x  x_{s}) c_{i}t (x  x_{s}) h_{im} (8)
where
c_{i}= 2.05  specific heat ice (kJ/kg^{o}C)
h_{im}= 335  melting heat of ice (kJ/kg)
Related Topics

Air Psychrometrics
Moist and humid air calculations. Psychrometric charts and Mollier diagrams. Aircondition systems temperatures, absolute and relative humidities and moisture content in air.
Related Documents

Air  Drying Force
The drying force of air depends on the air moisture holding capacity and the water surface to air evaporation capacity. 
Air  Humidifying by Adding Steam or Water
Air can be humidified by adding water or steam. 
Air  Humidifying with Steam, SI units
Using steam to humidify air. 
Air  Humidity Measurement from Dry and Wet Bulb Temperature
Relative humidity in moist air can estimated by measuring the dry and wet bulb temperature. 
Air  Humidity Ratio
The mass of water vapor present in moist air  to the mass of dry air. 
Air  Maximum Moisture Carrying Capacity
Maximum water content in humid air vs. temperature. 
Air  Specific Heat vs. Temperature at Constant Pressure
Online calculator with figures and tables showing specific heat (Cp and Cv) of dry air vs. temperature and pressure. SI and imperial units. 
Air  Thermophysical Properties
Thermal properties of air at different temperatures  density, viscosity, critical temperature and pressure, triple point, enthalpi and entropi, thermal conductivity and diffusivity and more. 
Air Cooling of Storage Roooms
Heat removed from storage rooms with cooled air. 
Air Heating Systems
Air heating buildings  heat supply vs. air flow and temperature. 
Cooling Tower Efficiency
Maximum cooling tower efficiency is limited by the cooling air wetbulb temperature. 
Dry Bulb, Wet Bulb and Dew Point Temperatures
Dry Bulb, Wet Bulb and Dew Point temperatures can be used to determine the state of humid air. 
Evaporation from a Water Surface
Evaporation of water from a water surface  like a swimming pool or an open tank  depends on water temperature, air temperature, air humidity and air velocity above the water surface  online calculator. 
Evaporative Cooling
Evaporative cooling tutorial. 
Great Sensible Heat Factor  GSHF
The Great Sensible Heat Factor is the ratio sensible to total heat in a cooling coil. 
Heat Recovery
Ventilation and heatrecovery calculations, sensible and latent heat  online calculators  imperial units. 
Heat Recovery Efficiency
Classification of heat recovery efficiencies  temperature efficiency, moisture efficiency and enthalpy efficiency  online heat exchanger efficiency calculator. 
Humid Air  Heating
Enthalpy change and temperature rise when heating humid air without adding moisture. 
Latent Heat Flow
Latent heat is the heat when supplied to or removed from air results in a change in moisture content  the temperature of the air is not changed. 
Mixing of Humid Air
The change in state wwhen mixing moist air  enthalpy, heat, temperature and specific humidity. 
Moist Air  Daltons Law of Partial Pressure
The pressure in a mixture of dry air and water vapor  humid or moist air  can be estimated by using Daltons Law of partial pressures. 
Moist Air  Degree of Saturation
Humidity ratio of moist air to humidity ratio of saturated moist air. 
Moist Air  Properties
Psychrometric table with humid air properties like saturation pressure, specific volume, enthalpy and entropy. 
Moist Air  Psychrometric Table for Pressure 29.92 inHg
Dry and wet bulb temperatures, saturation pressure, water vapor weight, specific volume, heat and more. 
Moist Air  Psychrometric Terms
Dry and wet bulb temperature, specific volume, relative humidity, enthalpy and more. 
Moist Air  Specific vs. Relative Humidity
Specific humidity of moist air vs. relative humidity, water vapor and air density. 
Removing Heat with Air
Calculating heat removed with air by measuring the wet bulb temperature. 
Water  Thermophysical Properties
Thermal properties of water at different temperatures like density, freezing temperature, boiling temperature, latent heat of melting, latent heat of evaporation, critical temperature and more. 
WaterSteam Mollier Diagram
Enthalpyentropy diagram for water and steam.