Great Sensible Heat Factor  GSHF
The Great Sensible Heat Factor is the ratio sensible to total heat in a cooling coil.
A cooling coil should have the capacity to handle the heat load generated in the room in addition the capacity to cool down the fresh make up air. The Great Sensible Factor is independent of the total air flow and can be expressed as
GSHF = [Q_{s} + m_{f} c_{p} (t_{f}  t_{r})] / [Q_{t} + m_{f} (h_{f}  h_{r})] (1)
where
GSHF = Great Sensible Heat Factor
Q_{s} = sensible heat generated in the room (kW)
m_{f} = fresh air mass flow (make up air) (kg/s)
c_{p} = specific heat of air (kg/kg.^{o}C)
t_{f} = temperature in fresh air (^{o}C)
t_{r} = temperature in room air (^{o}C)
Q_{t} = total heat generated in the room (kW)
h_{f} = specific enthalpy of fresh air (kJ/kg^{o}C)
h_{r} = specific enthalpy of air in the room (kJ/kg^{o}C)
Example  Great Sensible Heat Factor  GSHF
The sensible heat generation in a room is 4 kW and the latent heat generated is 1.4 kW. The room is cooled with an air flow of 1000 kg/h.
The fresh (out door) air temperature is 28^{o}C with a specific enthalpy of 60 kJ/kg and a humidity ratio of 12.7 g/kg.
The room temperature is 22^{o}C with a specific enthalpy of 45 kJ/kg and a specific humidity of 9.1 g/kg.
The Great Sensible Heat Factor can be calculated like
GSHF = [(4000 W) + (1000 kg/h)(1/3600 s/h)(1000 J/kg^{o}C)(28^{o}C  22^{o}C)] / [(4000 W + 1400 W) + (1000 kg/h)(1/3600 s/h)(60000 J/kg  45000 J/kg)]
= 0.59
Related Topics

Air Psychrometrics
Moist and humid air calculations. Psychrometric charts and Mollier diagrams. Aircondition systems temperatures, absolute and relative humidities and moisture content in air.
Related Documents

Air  Humidity Ratio
The mass of water vapor present in moist air  to the mass of dry air. 
Cooling and Heating Equations
Latent and sensible cooling and heating equations  imperial units. 
Cooling Load  Latent and Sensible Heat
Latent and sensible cooling loads to consider when designing HVAC systems. 
Humid Air  Heating
Enthalpy change and temperature rise when heating humid air without adding moisture. 
Latent Heat Flow
Latent heat is the heat when supplied to or removed from air results in a change in moisture content  the temperature of the air is not changed. 
Metabolic Heat Gain from Persons
Human metabolic heat gain in air conditioned rooms. 
Moist Air  Cooling and Dehumidifying
Cooling and dehumidifying processes of moist and humid air  sensible and latent cooling. 
Moist Air  Enthalpy
Sensible and latent heat of moist air. 
Room Sensible Heat Factor  RSHF
Room Sensible Heat Factor  RSHF  is defined as the sensible heat load divided by the total heat load in a room 
Sensible Heat Flow
Sensible heat is dry heat causing change in temperature but not in moisture content 
Sensible Heat Ratio  SHR
The ratio Sensible Heat (or Cooling) Load to the Total Heat (or Cooling) Load. 
Water  Thermophysical Properties
Thermal properties of water at different temperatures like density, freezing temperature, boiling temperature, latent heat of melting, latent heat of evaporation, critical temperature and more.