Ducts Sizing  the Velocity Reduction Method
The velocity reduction method can be used when sizing air ducts.
The Velocity Reduction Method can be used when sizing air ducts. The method can be summarized to
 Select suitable velocities for main and branch ducts from the table below
 Find the sizes of main and branch ducts from the air flow rates and the velocities by using eq. 1 and the charts below
 From velocities and duct dimensions  find the frictional pressure loss in the main and branch ducts using the friction chart below
 Add minor dynamic loss
Proper Velocities
A proper velocity depends on application and environment. The table below indicate commonly used velocities:
Type of Duct  Comfort Systems  Industrial Systems  High Speed Systems  

m/s  ftm  m/s  ftm  m/s  ftm  
Main ducts  4  7  780  1380  8  12  1575  2360  10  18  1670  3540 
Main branch ducts  3  5  590  985  5  8  985  1575  6  12  1180  2360 
Branch ducts  1  3  200  590  3  5  590  985  5  8  985  1575 
Be aware that high velocity close to outlets and inlets may generate unacceptable noise.
Velocities commonly used for different applications:
 upstream medium pressure VAV boxes: 2000 to 2500 fpm (10  13 m/s)
 transport of fumes, mist or very light particulates: 2400 fpm (12 m/s)
 dust collection systems with small particulate: 3500 fpm (18 m/s)
 dust collection systems with heavy particulate like metals: 5000 fpm (25 m/s)
Sizing Ducts
Sizes of ducts are then given by the continuity equation like:
A = q / v (1)
where
A = duct cross sectional area (m^{2})
q = air flow rate (m^{3}/s)
v= air speed (m/s)
Alternatively in Imperial units
A_{i} = 144 q_{i} / v_{i}_{ } (1b)
where
A = duct cross sectional area (sq.in.)
q = air flow rate (cfm)
v= air speed (fpm)
Frictional Pressure Loss
Estimate friction loss in main and branch ducts from the charts below:
Air Ducts Sizing Spreadsheet Template
Air Ducts Spreadsheet Template  The Velocity Method
The velocity method can be done manual or more or less semi automatic with the spreadsheet template below.
This template is based on the in the spreadsheet. Customize sections, airflows, duct sizes and minor dynamic loss coefficients  add pressure loss paths and evaluate and reconfigure the system to fit your criteria. Summarize pressure loss for each path and add damper pressure losses manually to balance the system.
The Google Docs spreadsheet template can be opened and copied here! The spreadsheet can also be downloaded as an excel file. Use the Google Docs "File" menu on the top of the template.
Insert air ducts to your Sketchup model with the Engineering ToolBox Sketchup Extension
Related Topics

Ventilation Systems
Design of systems for ventilation and air handling  air change rates, ducts and pressure drops, charts and diagrams and more.
Related Documents

Air Duct Velocities
Typical air duct velocities in applications like ventilation systems or compressed air systems. 
Air Ducts  Friction Loss Diagram
A major friction loss diagram for air ducts  Imperial units ranging 10  100 000 cfm. 
Air Ducts  Major Friction Head Loss, Online Calculator
Head loss or major loss in air ducts  equations and online calculator for rectangular and circular ducts  Imperial and SI units. 
Air Ducts  Sizing
Required duct area vs. air flow. 
Air Ducts  Velocity Diagram
Air flow volume, duct size, velocity and dynamic pressure. 
Design of Ventilation Systems
Design procedure for ventilation systems  air flow rates, heat and cooling loads, air shifts according occupants, air supply principles. 
Duct Sizing  the Equal Friction Method
The equal friction method for sizing air ducts is easy and straightforward to use. 
Duct Systems  Pressure Classifications
Duct systems are commonly divided into three pressure classifications. 
Duct Velocity
Calculate velocities in circular and rectangular ducts  imperial and SIunits  online calculator. 
Ducts  CrossSectional Area vs. Diameter
Circular ducts srosssectional areas. 
Ductwork  Supports
Recommended distance between ductwork support hangers. 
Dynamic Pressure
Dynamic pressure is the kinetic energy per unit volume of a fluid in movement. 
Equivalent Diameter  Rectangular vs. Circular HVAC Ducts
Rectangular equivalent diameter for air flows between 100  50000 cfm. 
Fluid Flow  Equation of Continuity
The Equation of Continuity is a statement of mass conservation. 
HVAC Abbreviations
Commonly used HVAC abbreviations. 
Noise generated in Air Ducts
Estimate noise generated by air flow in ducts. 
Sizing Circular Ducts
A rough guide to maximum air volume capacity of circular ducts in comfort, industrial and high speed ventilation systems. 
Spiral Ducts  Dimensions
Standard dimensions of spiral ducts  Imperial units. 
Velocity Classification of Ventilation Ducts
Recommended air velocities in ventilation ducts