# Total Pressure or Head Loss in Pipe or Duct Systems

## Major and minor loss in pipe, tubes and duct systems

The head loss of a pipe, tube or duct system, is the same as that produced in a straight pipe or duct whose length is equal to the pipes of the original systems plus the sum of the equivalent lengths of all the components in the system. This can be expressed as

hloss = Σ hmajor_losses + Σ hminor_losses                                           (1)

where

hloss = total head loss in the pipe or duct system

hmajor_losses = major loss due to friction in the pipe or duct system

hminor_losses = minor loss due to the components in the system

• Major Head Loss - head loss or pressure loss - due to friction in pipes and ducts.
• Minor Head Loss - head loss or pressure loss - due to components as valves, bends, tees and the like in the pipe or duct system.

### Summarized Major Losses

The major head loss for a single pipe or duct can be expressed as:

hmajor_loss = λ (l / dh) (v2 / 2 g)                                            (2)

where

hloss = head loss (m, ft)

λ = friction coefficient

l = length of duct or pipe (m)

dh = hydraulic diameter (m)

v = flow velocity (m/s, ft/s)

g = acceleration of gravity (m/s2, ft/s2)

### Summarized Minor Losses

Minor head loss can be expressed as:

hminor_loss = ξ v2/ 2 g                                            (3)

where

Since the velocity - v - in equation (2) in general is related to the pipe or duct where the component is located, the sum of the minor losses in a pipe or duct can be expressed as:

Σ hminor_losses = Σ ξ (v2/ 2 g)                                         (4)

The minor loss can be calculated by summarizing the minor loss coefficients - and multiplying the sum with the dynamic pressure head.

### Total Head Loss in a Single Pipe or Duct

The total head loss for a single pipe can be calculated by using equation (1) and (3):

hloss_single = λ (l / dh) (v2 / 2 g) + Σ ξ v2/ 2 g                                      (5)

or

hloss_single = (λ (l / dh) + Σ ξ ) (v2/ 2 g)                                          (6)

### Total Head Loss in Serial Connected Pipes

The total head loss in several serial connected pipes can be calculated by adding the total head loss in each pipe or duct. The total head loss can be expressed as:

hloss_serial = Σ [(λ1 (l1 / dh1) + Σ ξ1) (v12/ 2 g) + .. + λn (ln / dhn) + Σ ξn) (vn2/ 2 g)]                                     (7)

for 1 to n serial connected pipes

## Related Topics

• Fluid Mechanics - The study of fluids - liquids and gases. Involves velocity, pressure, density and temperature as functions of space and time
• Fluid Flow and Pressure Drop - Pipe lines - fluid flow and pressure loss - water, sewer, steel pipes, pvc pipes, copper tubes and more

## Search the Engineering ToolBox

- "the most efficient way to navigate!"

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your SketchUp model with the Engineering ToolBox - SketchUp Extension/Plugin - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

Translate the Engineering ToolBox!