Major and minor loss in pipe, tubes and duct systems
The head loss of a pipe, tube or duct system, is the same as that produced in a straight pipe or duct whose length is equal to the pipes of the original systems plus the sum of the equivalent lengths of all the components in the system. This can be expressed as
hloss = Σ hmajor_losses + Σ hminor_losses (1)
hloss = total head loss in the pipe or duct system
hmajor_losses = major loss due to friction in the pipe or duct system
hminor_losses = minor loss due to the components in the system
- Major Head Loss - head loss or pressure loss - due to friction in pipes and ducts.
- Minor Head Loss - head loss or pressure loss - due to components as valves, bends, tees and the like in the pipe or duct system.
Summarized Major Losses
The major head loss for a single pipe or duct can be expressed as:
hmajor_loss = λ (l / dh) (v2 / 2 g) (2)
hloss = head loss (m, ft)
l = length of duct or pipe (m)
dh = hydraulic diameter (m)
v = flow velocity (m/s, ft/s)
g = acceleration of gravity (m/s2, ft/s2)
Note! - the head unit is with reference to the density of the flowing fluid. For other units - like mm Water Column - check Velocity Pressure Head.
Summarized Minor Losses
Minor head loss can be expressed as:
hminor_loss = ξ v2/ 2 g (3)
Since the velocity - v - in equation (2) in general is related to the pipe or duct where the component is located, the sum of the minor losses in a pipe or duct can be expressed as:
Σ hminor_losses = Σ ξ (v2/ 2 g) (4)
The minor loss can be calculated by summarizing the minor loss coefficients - and multiplying the sum with the dynamic pressure head.
Total Head Loss in a Single Pipe or Duct
The total head loss for a single pipe can be calculated by using equation (1) and (3):
hloss_single = λ (l / dh) (v2 / 2 g) + Σ ξ v2/ 2 g (5)
hloss_single = (λ (l / dh) + Σ ξ ) (v2/ 2 g) (6)
Total Head Loss in Serial Connected Pipes
The total head loss in several serial connected pipes can be calculated by adding the total head loss in each pipe or duct. The total head loss can be expressed as:
hloss_serial = Σ [(λ1 (l1 / dh1) + Σ ξ1) (v12/ 2 g) + .. + λn (ln / dhn) + Σ ξn) (vn2/ 2 g)] (7)
for 1 to n serial connected pipes