Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

# Heat Transfer Coefficients in Heat Exchanger Surface Combinations

## Average overall heat transmission coefficients for fluid and surface combinations like Water to Air, Water to Water, Air to Air, Steam to Water and more.

The overall heat transfer coefficient is used to calculate total heat transfer through a wall or heat exchanger construction. The overall heat transfer coefficient depends on the fluids and their properties on both sides of the wall, the properties of the wall and the transmission surface.

For practically still fluids - average values for the overall heat transmission coefficient through different combinations of fluids on both sides of the wall and type of wall - are indicated in the table below:

Heat Transfer Coefficients in Heat Exchangers
FluidMaterial in Transmission SurfaceFluidOverall Heat Transmission Coefficient
- U -
(Btu/(ft2 hr oF))(W/(m2 K))
Water Cast Iron Air or Gas 1.4 7.9
Water Mild Steel Air or Gas 2.0 11.3
Water Copper Air or Gas 2.3 13.1
Water Cast Iron Water 40 - 50 230 - 280
Water Mild Steel Water 60 - 70 340 - 400
Water Copper Water 60 - 80 340 - 455
Air Cast Iron Air 1.0 5.7
Air Mild Steel Air 1.4 7.9
Steam Cast Iron Air 2.0 11.3
Steam Mild Steel Air 2.5 14.2
Steam Copper Air 3.0 17
Steam Cast Iron Water 160 910
Steam Mild Steel Water 185 1050
Steam Copper Water 205 1160
Steam Stainless Steel Water 120 680
• 1 Btu/ft2 hr oF = 5.678 W/m2 K = 4.882 kcal/h m2 oC - Unit Converter

Note that these coefficients are very rough. They depends on fluid velocities, viscosities, conditions of the heating surfaces, size of the temperature differences and so on. For exact calculations - always check manufacturing data.

### Example - Water to Air Heat Exchanger made in Copper

A roughly estimate of the specific heat transmission in a copper heat exchanger with water (mean temperature 80 oC) on one side and air (mean temperature 20 oC) on the other side - where the overall heat transfer coefficient U is 13.1 W/(m2 K) - can be calculated as

q = (13.1 W/(m2 K)) ((80 oC) - (20 oC))

= 786 W/m2

≈ 750 - 800 W/m2

## Related Topics

• ### Heating Systems

Design of heating systems - capacities and design of boilers, pipelines, heat exchangers, expansion systems and more.
• ### Insulation and Heat Loss from Steam and Condesate Pipe Lines

Heat loss from uninsulated and insulated steam and condensate pipes and tanks. Calculate insulation thicknesses.
• ### Steam and Condensate

Design of steam & condensate systems with properties, capacities, sizing of pipe lines, system configuration and more.
• ### Thermodynamics

Calculate heat, work, temperature and energy. The thermodynamics of steam and condensate systems. Water and Ice properties.
• ### Thermodynamics

Work, heat and energy systems.

## Related Documents

• ### Arithmetic and Logarithmic Mean Temperature Difference

Arithmetic Mean Temperature Difference in Heat Exchangers - AMTD - and Logarithmic Mean Temperature Difference - LMTD - formulas with examples - Online Mean Temperature Calculator.
• ### Condensation of Steam - Heat Transfer

Heat transfer when steam condensates.
• ### Convective Air Flow from Heat Source

Convective air flows from typical heat sources like people, computers, radiators and more.
• ### Convective Heat Transfer

Heat transfer between a solid and a moving fluid is called convection. This is a short tutorial about convective heat transfer.
• ### Cooling Mode - Heat Flux

Heat fluxes for various cooling or heat transfer modes.
• ### Copper Tubes - Uninsulated Heat Losses

Heat loss from uninsulated copper pipes - dimensions ranging 1/2 - 4 inches.
• ### Dowtherm A

Physical properties of Dowtherm A.
• ### Glycerine - Boiling and Freezing Points

Boiling and freezing points of glycerine aqueous solutions.
• ### Heat Exchangers - Fouling and Reduced Heat Transfer

Heat-transfer in heat exchangers are reduced by fouling.
• ### Heat Exchangers - Overall Heat Transfer Coefficients

Overall heat transfer coefficients in common heat exchanger designs - tubular, plate or spiral.
• ### Overall Heat Transfer Coefficients

Walls or heat exchangers - calculate overall heat transfer coefficients.
• ### Submerged Coils - Heat Transfer Coefficients

Heat transfer coefficients for steam and hot water coils submerged in oil tanks.
• ### Transmission Heat Loss through Building Elements

Heat loss through common building elements due to transmission, R-values and U-values - imperial and SI units.

## Search

Search is the most efficient way to navigate the Engineering ToolBox.

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with older versions of the amazing SketchUp Make and the newer "up to date" SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp Make/Pro from the Extension Warehouse !

We don't collect information from our users. More about

We use a third-party to provide monetization technologies for our site. You can review their privacy and cookie policy here.

You can change your privacy settings by clicking the following button: .

## Citation

• The Engineering ToolBox (2003). Heat Transfer Coefficients in Heat Exchanger Surface Combinations. [online] Available at: https://www.engineeringtoolbox.com/overall-heat-transfer-coefficients-d_284.html [Accessed Day Month Year].

Modify the access date according your visit.

7.25.9

.