Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

# Fluid Heat Transfer Coefficients in Heat Exchanger Surface Combinations

## Average overall heat transmission coefficients for fluid and surface combinations like Water to Air, Water to Water, Air to Air, Steam to Water and more.

The overall heat transfer coefficient is used to calculate total heat transfer through a wall or heat exchanger construction. The overall heat transfer coefficient depends on the fluids and their properties on both sides of the wall, the properties of the wall and the transmission surface.

For practically still fluids - average values for the overall heat transmission coefficient through different combinations of fluids on both sides of the wall and type of wall - are indicated in the table below:

FluidMaterial in Transmission SurfaceFluidOverall Heat Transmission Coefficient
- U -
(Btu/(ft2 hr oF))(W/(m2 K))
Water Cast Iron Air or Gas 1.4 7.9
Water Mild Steel Air or Gas 2.0 11.3
Water Copper Air or Gas 2.3 13.1
Water Cast Iron Water 40 - 50 230 - 280
Water Mild Steel Water 60 - 70 340 - 400
Water Copper Water 60 - 80 340 - 455
Air Cast Iron Air 1.0 5.7
Air Mild Steel Air 1.4 7.9
Steam Cast Iron Air 2.0 11.3
Steam Mild Steel Air 2.5 14.2
Steam Copper Air 3.0 17
Steam Cast Iron Water 160 910
Steam Mild Steel Water 185 1050
Steam Copper Water 205 1160
Steam Stainless Steel Water 120 680
• 1 Btu/ft2 hr oF = 5.678 W/m2 K = 4.882 kcal/h m2 oC - Unit Converter

Note that these coefficients are very rough. They depends on fluid velocities, viscosities, conditions of the heating surfaces, size of the temperature differences and so on. For exact calculations - always check manufacturing data.

### Example - Water to Air Heat Exchanger made in Copper

A roughly estimate of the specific heat transmission in a copper heat exchanger with water (mean temperature 80 oC) on one side and air (mean temperature 20 oC) on the other side - where the overall heat transfer coefficient U is 13.1 W/(m2 K) - can be calculated as

q = (13.1 W/(m2 K)) ((80 oC) - (20 oC))

= 786 W/m2

≈ 750 - 800 W/m2

## Related Topics

• Steam and Condensate - Steam & condensate systems- properties, capacities, pipe sizing, systems configuration and more.
• Heating - Heating systems - capacity and design of boilers, pipelines, heat exchangers, expansion systems and more.
• Thermodynamics - Thermodynamics of steam and condensate systems.
• Heat Loss and Insulation - Steam and condensate pipes - heat loss uninsulated and insulated pipes, insulation thickness and more.
• Thermodynamics - Work, heat and energy systems.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

## Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.

Temperature

oC
oF

Length

m
km
in
ft
yards
miles
naut miles

Area

m2
km2
in2
ft2
miles2
acres

Volume

m3
liters
in3
ft3
us gal

Weight

kgf
N
lbf

Velocity

m/s
km/h
ft/min
ft/s
mph
knots

Pressure

Pa (N/m2)
bar
mm H2O
kg/cm2
psi
inches H2O

Flow

m3/s
m3/h
US gpm
cfm

1 27