Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications! Heat loss (W/m) from 1/2 to 6 inches insulated pipes - ranging insulation thickness 10 to 80 mm and temperature differences 20 to 180 degC.
The heat loss diagrams below can be used to indicate the heat loss from insulated pipes at various temperature differences. The diagrams are based on
metal pipes fiber glass insulation with thermal conductivity 0.036 W/(mK) outdoor condition with moderate wind 9 m/s
A safety factor of
10% is included. indoor location - reduce values with 10% mineral wool insulation - increase values with 6% rigid cellular polyurethane - reduce values by 30% Heat loss diagram (W/m) Pipe Heat Loss - Insulation thickness 80 mm
1 W/m = 0.305 W/ft 1 oC = 1.8 oF Example - Heat Loss from Insulated Pipe Line
100 m of steel pipe with nominal dimension 2 1/2 inches is insulated with 80 mm fiber glass insulation. The temperature of the fluid in the pipe is 90 and the ambient temperature outside the pipe is oC 10 . oC
From the diagram above -
80 mm fiber glass insulation, temperature difference 80 and pipe dimension oC 2 1/2" - the heat loss is approximately 20 W/m.
The heat loss from the whole pipe can be calculated as
100 m) (20 W/m)
= 2000 W Pipe Heat Loss - Insulation thickness 50 mm
Pipe Heat Loss - Insulation thickness 40 mm
Pipe Heat Loss - Insulation thickness 30 mm
Pipe Heat Loss - Insulation thickness 25 mm
Pipe Heat Loss - Insulation thickness 20 mm
Pipe Heat Loss - Insulation thickness 10 mm
Related Topics Heat loss from pipes, tubes and tanks - with and without insulation - foam, fiberglass, rockwool and more. Steam and condensate pipes - heat loss uninsulated and insulated pipes, insulation thickness and more. Heat transfer and heat loss from buildings and technical applications - heat transfer coefficients and insulation methods to reduce energy consumption. Hot and cold water service systems - design properties, capacities, sizing and more. Related Documents Thermal conductivity of calcium silicate insulation - temperature and k-values. Heat loss from uninsulated copper tubes vs. temperature differences between tube and air. Heat loss from uninsulated copper pipes - dimensions ranging 1/2 - 4 inches. Thermal conductivity of fiberglass insulation - temperature and k-values. Heat loss from insulated and non insulated sheltered and exposed oil tanks and pipes. Wrapping factor when the heat loss from a pipe or tube is higher than the capacity of the heat trace cable. Hot water can be circulated through a return pipe if it's instantly required at the fixtures. Heat loss to surrounding air from insulated copper tubes. Thermal conductivity - k-values - vs. temperature. Heat loss from insulated and uninsulated, sheltered and exposed heated oil tanks. Heat loss (W/ft) diagrams for 1/2 to 6 inches insulated pipes - ranging insulation thickness 0.5 to 4 inches and temperature differences 50 to 350 degF. Conductive heat losses through cylinder or pipe walls. Thermal conductivity - k-values - vs. temperature. The amount of condensate generated in a steam pipe depends on the heat loss from the pipe to the surroundings. Heat losses from un-insulated steam pipes. Steam tracing of pipe lines can be done to maintain appropriate product temperatures. Heat loss from steel pipes and tubes - dimensions 1/2 to 12 inches. Search
Search is the most efficient way to navigate the Engineering ToolBox.
About the Engineering ToolBox!
We don't collect information from our users. More about
This page can be cited as
The Engineering ToolBox (2008). Pipes - Insulated Heat Loss Diagrams. [online] Available at: https://www.engineeringtoolbox.com/heat-loss-insulated-pipes-d_1151.html [Accessed Day Month Year].
Modify the access date according your visit.