Typical required water supply to public buildings:
- 1 gpm =6.30888x10-5 m3/s = 0.227 m3/h
Hot and cold water service systems - design properties, capacities, sizing and more.
Design procedures for domestic hot water service systems.
Introduction to general design of domestic service water supply systems - with pressurized or gravity tanks.
Lime deposited vs. temperature and water consumption.
Recommended dimensions hot and cold water pipes.
Nominal pipe size, outside diameter, wall thickness, weight and working pressure.
Tags and label colors used for mechanical, plumbing and piping systems.
Calculating expected demand for water supply service lines.
It is fundamental to keep the potable water in the water supply systems uncontaminated.
Supply requirements for common fixtures.
Converting WSFU - Water Supply Fixture Units - to GPM.
WSFU is used to calculate water supply service systems.
Sizing water supply service and distribution lines based on Water Supply Fixture Units (WSFU).
Sizing of water supply pipe lines.
Typiclal limits for impurities in drinking water.
Free online tool for designing water supply systems in buildings.