Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

# Steam Pipes - Online Pressure drop Calculator

## Calculate pressure drops in steam distribution pipe lines.

The pressure drop in a saturated steam distribution pipe line can be calculated in metric units as

dp = 0.6753 106 q2 l (1 + 91.4/d) / ρ d5                                           (1)

where

dp = pressure drop (Pa)

q = steam flow rate (kg/h)

l = length of pipe (m)

d = pipe inside diameter (mm)

ρ = steam density (kg/m3)

The Unwin formula can also be expressed in imperial units as

dp = 0.0001306 q2 l (1 + 3.6/d) / (3600 ρ d5)                                                  (2)

where

dp = pressure drop (psi)

q = steam flow rate (lb/hr)

l = length of pipe (ft)

d = pipe inside diameter (inches)

ρ = steam density (lb/ft3)

Use values for the specific volume corresponding to the average pressure if the pressure drop exceeds 10 - 15 % of the initial absolute pressure.

Note that for elevated velocities the Unwin's formula is known to give pressure drops higher than the actual.

### Example - Pressure Drop in a Steam Pipe

A steam flow 4000 kg/h with pressure 10 bar (1000 kPa) and density 5.15 kg/m3 flows through a schedule 40 ND 100 steel pipe with inside diameter 102 mm and length 100 m. The pressure drop can be calculated as

dp = 0.6753 106  (4000 kg/h)2  (100 m) (1 + 91.4/(102 mm)) / ((5.15 kg/m3)  (102 mm)5 )

= 36030 Pa

= 36 kPa

### Steam Pressure Drop Calculator - Metric Units

Steam flow rate - q (kg/h)

Length of pipe - l (m)

Pipe inside diameter - d (mm)

Steam density (kg/m3)

### Steam Pressure Drop Calculator - Imperial Units

Steam flow rate - q (lb/h)

Length of pipe - l (ft)

Pipe inside diameter - d (in)

Steam density (lb/ft3)

#### Pressure Drop Diagrams - metric units

The diagrams below can be used to indicate pressure drop in steam pipes at different pressures. The calculations are made for schedule 40 pipe.

• 1 bar = 100 kPa = 10,197 kp/m2 = 10.20 m H2O = 0.9869 atm = 14.50 psi (lbf/in2)
• 1 kg/h = 2.778x10-4 kg/s = 3.67x10-2 lb/min

## Related Topics

• Steam and Condensate - Steam & condensate systems- properties, capacities, pipe sizing, systems configuration and more.
• Pipe Sizing - Sizing of steam and condensate pipe lines - pressure loss, recommended velocity, capacity and more.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

## Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.

Temperature

oC
oF

Length

m
km
in
ft
yards
miles
naut miles

Area

m2
km2
in2
ft2
miles2
acres

Volume

m3
liters
in3
ft3
us gal

Weight

kgf
N
lbf

Velocity

m/s
km/h
ft/min
ft/s
mph
knots

Pressure

Pa (N/m2)
bar
mm H2O
kg/cm2
psi
inches H2O

Flow

m3/s
m3/h
US gpm
cfm

1 27