# Steam Pipes - Sizing

The pressure available for distribution of steam is the pressure difference between the initial pressure at the boiler, and the required final pressure at the end of the line - at the steam consumer.

The pressure difference available for the distribution system can be expressed as:

p = p_{j}- p_{k}(1)

where

p = available pressure drop (Pa (N/m^{2}), psi (lb/ft^{2}))

p_{j}= initial or boiler pressure (Pa (N/m^{2}), psi (lb/ft^{2}))

p_{k}= final pressure (Pa (N/m^{2}), psi (lb/ft^{2}))

The total pressure drop in the distribution system is a result of friction (major loss) and pressure loss in fittings (minor loss), and can be expressed as:

p_{t}= p_{major}+ p_{minor}(2)

where

p_{t}= total pressure drop in the system (Pa (N/m^{2}), psi (lb/ft^{2}))

p_{major}= pressure loss in pipes due to friction (Pa (N/m^{2}), psi (lb/ft^{2}))

p_{minor}= pressure loss in fittings (Pa (N/m^{2}), psi (lb/ft^{2}))

### Friction - Major Loss

Major loss - the pressure loss due to friction in a low pressure steam distribution system can be expressed as:

p_{major}= p_{a}l (3)

where

p_{a}= pipe friction resistance per unit length of pipe (Pa/m (N/m^{2}/m), psi/ft (lb/ft^{2}/ft))

l = length of pipe (ft, m)

The pressure drop in a steam pipe can be expressed as

p_{a-100}= 0.01306 q^{2}(1 + 3.6/d_{i}) / (3600ρ d_{i}^{5}) (3b)

where

p_{a-100}= pressure drop per 100 ft pipe (psig / 100 ft)

q = steam flow rate (lb/h)

d_{i}= inside diameter of pipe (in)

ρ = density of steam (lb/ft^{3})

### Loss due to Fittings - Minor loss

Loss due to fittings - minor loss can be expressed as:

p_{minor}= ξ 1/2ρ v^{2}(4)

where

ξ = minor loss coefficient

p_{minor}= pressure loss (Pa (N/m^{2}), psi (lb/ft^{2}))

ρ = density (kg/m^{3}, slugs/ft^{3})

v = flow velocity (m/s, ft/s)

### Equivalent length

Minor loss - loss due to fittings can also be expressed as equivalent length:

p_{minor}= p_{a}l_{e}(5)

or

p_{t}= p_{a}(l + l_{e}) (6)

where

l_{e}= equivalent length of the fittings (ft, m)

As a rule of thumb the total pressure drop is about* 5 -10%* of initial pressure per *100 m* pipe.

### Typical Steam Velocities

- Exhaust steam -
*20 to 30 m/s (70 - 100 ft/s)* - Saturated steam -
*30 to 40 m/s (100 - 130 ft/s)* - Superheated steam -
*40 to 60 m/s (130 -200 ft/s)*

## Related Topics

### • Pipe Sizing

Sizing of steam and condensate pipe lines - pressure loss, recommended velocity, capacity and more.

### • Steam and Condensate

Steam & condensate systems- properties, capacities, pipe sizing, systems configuration and more.

## Related Documents

### ANSI Schedule 40 Steel Pipes - Dimensions

Internal and external diameters, areas, weights, volumes and number of threads for ANSI schedule 40 steel pipes.

### Condensate Pipe Lines - Sizing

Flow and pressure loss in condensate return lines - SI Units.

### Horizontal Pipe Hanger Supports - Spacing and Rod Size

Recommended maximum support span between hangers - and rod sizes for straight horizontal pipes.

### Insulated Steam Pipes - Condensate Generated (kg/h per 100m)

Heat loss from steam pipes generates condensate which must be drained from the system.

### Recommended Velocities in Steam Systems

The steam velocity in a steam distribution system should be within certain limits to avoid excessive wear and tear

### Sizing Steam Pipes (kg/h)

Steam is a compressible gas where pipe line mass flow capacity depends on steam pressure.

### Sizing Steam Pipes (lb/h)

Steam is a compressible gas where the capacity of a pipe line depends on the size of the pipe and the steam pressure.

### Steam Flow Rate vs. Pressure Drop - Schedule 40 Pipe

Flow rate *(lb/h)* and pressure drop per* 100 feet* of pipe.

### Steam Heating Processes - Load Calculating

Calculating the amount of steam in non-flow batch and continuous flow heating processes.

### Steam Heating Systems - Design

An introduction to the basic design of steam heating systems.

### Steam Pipes - Installation of Drip Legs

Properly draining steam pipes for condensate.

### Steam Pipes - Online Pressure drop Calculator

Calculate pressure drops in steam distribution pipe lines.

### Steam Pipes - Pressure Drop vs. Steam Flow

Steam pipes and pressure drop diagrams - imperial and metric units.

### Steam Trap Selection Guide

Steam trap selection guide - Float & Thermostatic, Inverted Bucket, Bimetal Thermostatic, Impulse and Thermodynamic Disc steam traps.

### Steel Pipes - Thermal Expansion Loops

Calculating and sizing steel pipe thermal expansion loops.

### Thermal Expansion of Steam Pipes - (inches)

Expansion of steam pipes heated from room temperature to operation temperature.