# Humid Air - Heating

The process of ** sensible heating ** of air - heating without adding moisture - can be visualized in the Mollier diagram as:

Sensible heating of air changes the state of the air from A to B along the constant specific humidity - * x * - line. The supplied heat - * dH * - can be estimated as indicated in the diagram above.

The heating process can also be visualized in the psychrometric chart

Note! - when sensible heating of air - the specific moisture remains constant - the relative humidity is decreased.

### Calculating Enthalpy

The enthalpy of moist air can be calculated as:

h = c_{ pa }t + x [c_{ pw }t + h_{ we }](1)

where

h= specific enthalpy of moist air (kJ/kg)

c_{ pa }= 1.01 - specific heat capacity of air at constant pressure (kJ/kg^{o}C, kWs/kgK)

t= air temperature (^{o}C)

x= humidity ratio (kg/kg)

c_{ pw }= 1.84 - specific heat capacity of water vapor at constant pressure (kJ/kg.^{o}C, kWs/kg.K)

h_{ we }= 2502 - evaporation heat of water at 0^{o}C (kJ/kg)

(1) can be modified to:

h = 1.01 (kJ/kg.^{o}C) t + x [1.84 (kJ/kg.^{o}C) t + 2502 (kJ/kg)](1b)

### The Enthalpy Difference

The enthalpy difference when heating air without adding moisture can be calculated as:

dh_{ A-B }= c_{ pa }t_{ B }+ x [c_{ pw }t_{ B }+ h_{ we }] - c_{ pa }t_{ A }+ x [c_{ pw }t_{ A }+ h_{ we }]

= c_{ pa }(t_{ B }- t_{ A }) + x c_{ pw }(t_{ B }- t_{ A })(2)

#### Example - Enthalpy Change when Heating Air

The specific humidity of air at 25 ^{o}C and relative moisture * 50% * is * 0.0115 kg/kg * - check the Mollier diagram . The change in enthalpy when heating the air to * 35 ^{o}C * can be calculated as:

dh_{ A-B }=(1.01 kJ/kg^{o}C)(35^{o}C - 25^{o}C) + (0.0115 kg/kg) (1.84 kJ/kg^{o}C) (35^{o}C - 25^{o}C)

= (10.1 kJ/kg) + (0.2 kJ/kg)

= 10.3 (kJ/kg)

** Note! ** - the contribution from the water vapor is relatively small and can for practical purposes often be neglected. (2) can then be modified to:

dh_{ A-B }= c_{ pa }( t_{ B }- t_{ A })(2b)

### Increase in Temperature when Heating Air

If heat is added to humid air the increase in air temperature can be calculated by modifying * (2b) * to:

t_{ B }- t_{ A }= dh_{ A-B }/ c_{ pa }(2c)

#### Example - Heating Air and Temperature Rise

If * 10.1 kJ * is added to * 1 kg * air the temperature rise can be calculated as:

t_{ B }- t_{ A }=(10.1 kJ/kg) / (1.01 kJ/kg^{o}C)

= 10 (^{o}C)

### Heat Flow in a Heating Coil

The total heat flow rate through a heating coil can be calculated as:

q = m (h_{ B }- h_{ A })(3)

where

q= heat flow rate (kJ/s, kW)

m= mass flow rate of air (kg/s)

The total heat flow can also be expressed as:

q_{ s }= L ρ (h_{ B }- h_{ A })(3a)

where

L= air flow rate (m^{3}/s)

ρ= density of air (kg/m^{3})

** Note! ** The density of air varies with temperature. At * 0 ^{o}C * the density is

*1.293 kg/m*. At

^{3}*80*the density is

^{o}C*1.0 kg/m*.

^{3}It's common to express sensible heat flow rate as:

q = m c_{ pa }(t_{ B }- t_{ A })(3b)

or alternatively:

q = L ρ c_{ pa }(t_{ B }- t_{ A })(3c)

### Heating Coil Effectiveness

For a limited heating coil surface the average surface temperature will always be higher than the outlet air temperature. The effectiveness of a heating coil can be expressed as:

μ = (t_{ B }- t_{ A }) / (t_{ HC }- t_{ A })(4)

where

μ= heating coil effectiveness

t_{ HC }= mean surface temperature of the heating coil (^{o}C)

### Example - Heating Air

* 1 m ^{3} /s * of air at

*15*and relative humidity

^{o}C*60%*(A) is heated to

*30*(B). The surface temperature of the heating coil is

^{o}C*80*. The density of air at

^{o}C*20*is

^{o}C*1.205 kg/m*.

^{3}From the Mollier diagram the enthalpy in (A) is * 31 kJ/kg * and in (B) * 46 kJ/kg *.

The heating coil effectiveness can be calculated as:

μ =(30^{o}C - 15^{o}C) / (80^{o}C - 15^{o}C)

= 0.23

The heat flow can be calculated as:

q =(1 m^{3}/s) (1.205 kg/m^{3}) ((46 kJ/kg) - (31 kJ/kg))

= 18 (kJ/s, kW)

As an alternative, as one of the most common methods:

q =(1 m^{3}/s) (1.205 kg/m^{3}) (1.01 kJ/kg.^{o}C) (30^{o}C - 15^{o}C)

= 18.3 (kJ/s, kW)

** Note! ** Due to the inaccuracy when working with diagrams there is a small difference between the total heat flow and the sum of the latent and sensible heat. In general - this inaccuracy is within acceptable limits.

## Related Topics

### • Air Psychrometrics

Moist and humid air calculations. Psychrometric charts and Mollier diagrams. Air-condition systems temperatures, absolute and relative humidities and moisture content in air.

## Related Documents

### Air - Drying Force

The drying force of air depends on the air moisture holding capacity and the water surface to air evaporation capacity.

### Air - Heating, Cooling, Mixing, Humidifying or Dehumidifying Processes

Basic air changing state processes - heating, cooling, mixing, humidifying and dehumidifying by adding steam or water - psychometric diagrams and the Mollier charts.

### Air - Humidifying with Steam, SI units

Using steam to humidify air.

### Air - Humidity Measurement from Dry and Wet Bulb Temperature

Relative humidity in moist air can estimated by measuring the dry and wet bulb temperature.

### Air - Maximum Moisture Carrying Capacity

Maximum water content in humid air vs. temperature.

### Air - Specific Heat vs. Temperature at Constant Pressure

Online calculator with figures and tables showing specific heat (Cp and Cv) of dry air vs. temperature and pressure. SI and imperial units.

### Air - Thermal Conductivity vs. Temperature and Pressure

Online calculator with figures and tables showing air thermal conductivity vs. temperature and pressure. SI and imperial units.

### Air - Thermophysical Properties

Thermal properties of air at different temperatures - density, viscosity, critical temperature and pressure, triple point, enthalpi and entropi, thermal conductivity and diffusivity and more.

### Air Cooling of Storage Roooms

Heat removed from storage rooms with cooled air.

### Air Heating Systems

Air heating buildings - heat supply vs. air flow and temperature.

### Cooling and Heating Equations

Latent and sensible cooling and heating equations - imperial units.

### Cooling Load - Latent and Sensible Heat

Latent and sensible cooling loads to consider when designing HVAC systems.

### Dry Air - Thermodynamic and Physical Properties

Thermodynamic properties of dry air - specific heat, ratio of specific heats, dynamic viscosity, thermal conductivity, Prandtl number, density and kinematic viscosity at temperatures ranging *175 - 1900 K*.

### Great Sensible Heat Factor - GSHF

The Great Sensible Heat Factor is the ratio sensible to total heat in a cooling coil.

### Heat Recovery

Ventilation and heat-recovery calculations, sensible and latent heat - online calculators - imperial units.

### Heat Recovery Efficiency

Classification of heat recovery efficiencies - temperature efficiency, moisture efficiency and enthalpy efficiency - online heat exchanger efficiency calculator.

### Latent Heat Flow

Latent heat is the heat when supplied to or removed from air results in a change in moisture content - the temperature of the air is not changed.

### Moist Air - Cooling and Dehumidifying

Cooling and dehumidifying processes of moist and humid air - sensible and latent cooling.

### Moist Air - Enthalpy

Sensible and latent heat of moist air.

### Removing Heat with Air

Calculating heat removed with air by measuring the wet bulb temperature.

### Steam Heating Air

Calculate steam heated air systems.