Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

# Heat Recovery

## Ventilation and heat-recovery calculations, sensible and latent heat - online calculators - imperial units.

A heat-recovery system captures building exhaust air and reuse some of the energy to precondition the make-up air before supplying it to the building.

Air-to-air heat-recovery systems for comfort applications can in general be categorized as

• sensible heat (dry bulb only) systems
• total heat (wet bulb - sensible heat plus latent heat) systems

### Sensible Heat-Recovery Systems

A sensible heat-recovery systems will transfer sensible (dry-bulb) heat from the exhaust air to the supply air entering the building. Rotary wheel heat exchangers and cross flow heat exchangers are some of the common designs used in typical comfort-to-comfort sensible heat-recovery applications.

The amount of heat transferred can be expressed as

H = 1.08 q (t2 - t1) η                                            (1)

where

H = heat transferred (Btu/h)

q = quantity of airflow (cfm)

t1 = air temperature of the exhaust air before the heat recovery unit (oF)

t2 = air temperature of outside air after the heat recovery unit (oF)

η = heat-recover efficiency

### Example - A Sensible Heat Recovery System

The outside air temperature is 90ºF and the exhaust air temperature is 75ºF. The system operates at 40,000 cfm at 73 percent efficiency.

The sensible heat-recovery can be expressed as

H = 1.08 (40000 cfm) ((90 oF) - (75 oF)) 0.73

= 473040 (Btu/h)

### A Sensible Heat Recovery Calculator

The calculator below can be used to calculate the sensible heat recovery where the air flow, outside and inside temperature and recovery efficiency are known.

q - air flow (cfm)

t1 - outside air temperature before the heat exchanger (oF)

t2 - outside air temperature after the heat exchanger (oF)

η - heat recovery unit efficiency

### Total Enthalpy Heat Recovery System

For total enthalpy heat-recovery systems the heat recovered can be expressed as

H = 4.5 q (h2 - h1) η                                          (2)

where

4.5 = (0.075 lbm/ft3) (60 min/h)

h1 = air enthalpy of the exhaust air before the heat recovery unit (Btu/lb)

h2air enthalpy of outside air after the heat recovery unit (Btu/lb)

### Related Mobile Apps from The Engineering ToolBox

- free apps for offline use on mobile devices.

### Example - Total Enthalpy Heat Recovery System

The outside air wet-bulb temperature is 70ºF (enthalpy 34 Btu/lb) and the exhaust-air wet-bulb temperature is 60ºF (enthalpy 26.4 Btu/lb). The system operates at 40,000 cfm at 73 percent efficiency.

The total heat-recovery can be expressed like

H = 4.5 (40000 cfm) ((34 Btu/lb) - (26.4 Btu/lb)) 0. 73

= 998640 (Btu/h)

### A Total Heat Recovery Calculator

The calculator below can be used to calculate the total (latent and sensible) heat recovery where the air flow, enthalpy of outside and inside air and the recovery efficiency are known.

q - air flow (cfm)

h2 - enthalpy outside air before the heat recovery unit (Btu/lb)

h1 - enthalpy outside air after the heat recovery unit (Btu/lb)

η - heat recovery unit efficiency

## Related Topics

• Ventilation - Systems for ventilation and air handling - air change rates, ducts and pressure drops, charts and diagrams and more.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

## Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.

Temperature

oC
oF

Length

m
km
in
ft
yards
miles
naut miles

Area

m2
km2
in2
ft2
miles2
acres

Volume

m3
liters
in3
ft3
us gal

Weight

kgf
N
lbf

Velocity

m/s
km/h
ft/min
ft/s
mph
knots

Pressure

Pa (N/m2)
bar
mm H2O
kg/cm2
psi
inches H2O

Flow

m3/s
m3/h
US gpm
cfm

6 24