Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

## Calculating chiller and cooling tower refrigeration loads - in tons.

Cooling towers tons pairs the water-cooled chiller tons and the water-cooled condenser tons.

### Chiller Refrigeration Tons

The process of cooling is called refrigeration. For commercial and industrial refrigeration systems most of the world uses the kilowatt (kW) as the basic unit of refrigeration. Some commercial and industrial refrigeration systems are rated in Tons of Refrigeration (TR, tons).

A water-chiller refrigeration ton is defined as:

1 Refrigeration Ton (RT) = 1 TONScond = 12000 Btu/h = 200 Btu/min = 3025.9 k Calories/h = 12661 kJ/h = 3.517 kW

1 kW = 0.2843 Refrigeration Ton (RT)

A ton is the amount of heat removed by an air conditioning system that would melt 1 ton (2000 lbs.) of ice in 24 hours. The heat required to melt 1 lb of ice at 32 oF to water is 144 Btu.

1 Ton Refrigeration = (2000 lb) (144 Btu/lb) / (24 hr)

= 12000 Btu/hr

#### Converting between Btu/h and Tons of Refrigeration

Btu/hRefrigeration TonkW
6000 1/2 1.76
12000 1 3.52
18000 1 1/2 5.28
24000 2 7.03
30000 2 1/2 8.79
36000 3 10.6
42000 3 1/2 12.3
48000 4 14.1
54000 4 1/2 15.8
60000 5 17.6

### Cooling Tower Tons

A cooling tower ton is defined as:

1 cooling tower ton = 1 TONSevap = 1 TONScond x 1.25 = 15000 Btu/h = 3782 k Calories/h = 15826 kJ/h = 4.396 kW

The equivalent ton on the cooling tower side actually rejects about 15000 Btu/h due to the heat-equivalent of the energy needed to drive the chiller's compressor. This equivalent ton is defined as the heat rejection in cooling 3 U.S. gallons/minute (1500 pound/hour) of water 10°F, which amounts to 15000 Btu/hour, or a chiller coefficient-of-performance (COP) of 4.0 - a COP equivalent to an energy efficiency ratio (EER) of 13.65.

### Heat Load and Water Flow

A water systems heat load in Btu/h can be simplified to:

h = cp ρ q dt

= (1 Btu/lbm oF) (8.33 lbm/US gal) q (60 min/h) dt

= 500 q dt                                                                  (1)

where

cp = specific heat, 1 (Btu/lbm oF) for water

ρ = 8.33 (lbm/US gal) for water

q = water volume flow rate (US gal/min)

dt = temperature difference (oF)

### Example - Water Chiller Cooling

Water flows with 1 gal/min and 10oF temperature difference. The ton of cooling load can be calculated as:

h = 500 (1 US gal/min) (10 oF)

= 5000 Btu/h

= (5000 Btu/h) / (12000 Btu/ton)

= 0.42 ton

(ft2/ton)
Arenas 150 - 200
Classroom 200 - 250
Clean room 100 - 300
Conference room 100 - 200
Data room 80 - 100
Meeting room 200 - 250
Office 300 - 350
Residence 600 - 700

## Related Topics

• Air Conditioning - Air Conditioning systems - heating, cooling and dehumidification of indoor air for thermal comfort.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

## Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.

Temperature

oC
oF

Length

m
km
in
ft
yards
miles
naut miles

Area

m2
km2
in2
ft2
miles2
acres

Volume

m3
liters
in3
ft3
us gal

Weight

kgf
N
lbf

Velocity

m/s
km/h
ft/min
ft/s
mph
knots

Pressure

Pa (N/m2)
bar
mm H2O
kg/cm2
psi
inches H2O

Flow

m3/s
m3/h
US gpm
cfm

3 10