Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

# Cooling Load - Convert between kW/ton to COP or EER

## Convert between cooling load units like kW/ton, COP and EER.

Chiller efficiency depends on heat removed and energy consumed.

Absorption chillers are often rated in fuel consumption per ton cooling. Electric motor driven chillers are rated in kilowatts per ton cooling.

• kW/ton = 12 / EER
• kW/ton = 12 / (COP x 3.412)
• COP = EER / 3.412
• COP = 12 / (kW/ton) / 3.412
• EER = 12 / (kW/ton)
• EER = COP x 3.412

If the efficiency of a chiller is rated to 1 kW/ton, then

• COP = 3.52
• EER = 12

### Cooling Load in - kW/ton

The term kW/ton is commonly used for larger commercial and industrial air-conditioning, heat pump and refrigeration systems.

The term is defined as the ratio of energy consumption in kW to the rate of heat removal in tons at the rated condition. The lower the kW/ton - the more efficient the system.

kW/ton = Pc / Qr                                                                  (1)

where

Pc = electrical power consumption (kW)

### Coefficient of Performance - COP

The Coefficient of Performance - COP - is the basic parameter used to report efficiency of refrigerant based systems. COP is the ratio between useful cooling or heating output and power input and can be expressed as

COP = Pc / P                                                     (2)

where

COP = Coefficient of Performance

Pc = useful cooling or heating power output (Btu/h, W)

P = power input (Btu/h, W)

The COP is an instantaneous measurement in that the units are power which can be measured at one point in time. COP can be used to define the cooling efficiency for a cooling system - or the heating efficiency for a heat pump system.

• CoolingCOP is defined as the ratio of of the heat removal to the power input to the compressor
• Heating - COP is defined as the ratio of the heat delivered to the power input to the compressor
• higher COP - more efficient system

COP can be treated as an efficiency where COP of 2.0 = 200% efficiency. For unitary heat pumps, ratings at two standard outdoor temperatures of 47oF and 17oF (8.3oC and -8.3oC) are typically used.

### Example - COP for an Air Conditioner Unit

At an instantaneous moment an air conditioner units cools air from 30 oC and 70% moisture to 20 oC and 100% moisture. The air flow through the unit is 0.1 m3/s and the electrical power consumption of the unit is 600 W.

From the Mollier diagram  we can see that the enthalpy of the input air is aprox. 78 kJ/kg and the enthalpy of the output air is aprox. 57 kJ/kg.

The heat removed from the air can be calculated as

Pc = ((78 kJ/kg) - (57 kJ/kg)) (0.1 m3/s) (1.2 kg/m3)

= 2.5 kW

COP for the unit can be calculated as

COP = (2.5 kW) / (0.6 kW)

= 4.2

### Example - COP for a Heat Pump

A heat pump delivers 4.8 kW (16378 Btu/h) of heat with electric power consumption 1.2 kW (4094 Btu/h). COP for the heat pump at the actual conditions can be calculated  as

COP = (4.8 kW) / (1.2 kW)

= 4

### Energy Efficiency Ratio - EER

The Energy Efficiency Ratio - EER - is a term generally used to define cooling energy efficiency of unitary air-conditioning and heat pump system.

The efficiency is determined at a single rated condition specified by an appropriate equipment standard and is defined as the ratio of net cooling capacity - or heat removed in Btu - to the total input rate of electric energy applied - in Wh. The units of EER are Btu/Wh.

EER = Qc / E                                                          (3)

where

EER = energy efficient ratio (Btu/Wh)

Qc = net cooling energy (Btu)

E = applied electrical energy (Wh)

This efficiency term typically includes the energy requirement of auxiliary systems such as the indoor and outdoor fans.

• higher EER -  more efficient system

#### Example - EER for an Air Conditioner Unit

The heat removed and electrical power consumed for the air conditioner unit can be measured and calculated in different ways. One simple alternative is to calculate mean values from some instantaneous samples.

Time
(h)
Instantaneous Heat Removed
Pc
(Btu/h)
Instantaneous Electrical Power
P
(W)
0 8500 600
1 10000 700
2 7000 550

The heat removed for 3 hours can be estimated to

Qc = ((8500 Btu/h + 10000 Btu/h + 7000 Btu/h) / 3) (3 h)

= 25500 Btu

The electrical consumption for 3 hours can be estimated to

E = ((600 W + 700 W + 550 W) / 3) (3 h)

= 1850 Wh

EER for the air conditioner unit can be estimated to

EER = (25500 Btu) / (1850 Wh)

= 13.8

## Related Topics

• Air Conditioning - Air Conditioning systems - heating, cooling and dehumidification of indoor air for thermal comfort.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

## Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.

Temperature

oC
oF

Length

m
km
in
ft
yards
miles
naut miles

Area

m2
km2
in2
ft2
miles2
acres

Volume

m3
liters
in3
ft3
us gal

Weight

kgf
N
lbf

Velocity

m/s
km/h
ft/min
ft/s
mph
knots

Pressure

Pa (N/m2)
bar
mm H2O
kg/cm2
psi
inches H2O

Flow

m3/s
m3/h
US gpm
cfm

6 24