Calculating chiller and cooling tower refrigeration loads - in tons.
Cooling towers tons pairs the water-cooled chiller tons and the water-cooled condenser tons.
Chiller Refrigeration Tons
The process of cooling is called refrigeration. For commercial and industrial refrigeration systems most of the world uses the kilowatt (kW) as the basic unit of refrigeration. Some commercial and industrial refrigeration systems are rated in Tons of Refrigeration (TR, tons).
A water-chiller refrigeration ton is defined as:
1 kW = 0.2843 Refrigeration Ton (RT)
A ton is the amount of heat removed by an air conditioning system that would melt 1 ton (2000 lbs.) of ice in 24 hours. The heat required to melt 1 lb of ice at 32 o F to water is 144 Btu.
1 Ton Refrigeration = (2000 lb) (144 Btu/lb) / (24 hr)
= 12000 Btu/hr
Converting between Btu/h and Tons of Refrigeration
Cooling Tower Tons
A cooling tower ton is defined as:
The equivalent ton on the cooling tower side actually rejects about 15000 Btu/h due to the heat-equivalent of the energy needed to drive the chiller's compressor. This equivalent ton is defined as the heat rejection in cooling 3 U.S. gallons/minute (1500 pound/hour) of water 10°F , which amounts to 15000 Btu/hour , or a chiller coefficient-of-performance ( COP ) of 4.0 - a COP equivalent to an energy efficiency ratio ( EER ) of 13.65 .
Heat Load and Water Flow
A water systems heat load in Btu/h can be simplified to:
h = c p ρ q dt
= (1 Btu/lb m o F) ( 8.33 lb m /US gal) q (60 min/h) dt
= 500 q dt (1)
h = heat load (Btu/h)
c p = specific heat, 1 (Btu/lb m o F) for water
q = water volume flow rate (US gal/min)
dt = temperature difference ( o F)
Example - Water Chiller Cooling
Water flows with 1 gal/min and 10 o F temperature difference. The ton of cooling load can be calculated as:
h = 500 (1 US gal/min) (10 o F)
= 5000 Btu/h
= (5000 Btu/h) / (12000 Btu/ton)
= 0.42 ton
Typical Cooling Loads
|Type of Room||Cooling Load |
(ft 2 /ton)
|Arenas||150 - 200|
|Classroom||200 - 250|
|Clean room||100 - 300|
|Conference room||100 - 200|
|Data room||80 - 100|
|Meeting room||200 - 250|
|Office||300 - 350|
|Residence||600 - 700|