Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications! The working pressure and temperature limits of ASME Code B31.9 - Building Services Piping.
ASME B31.9 Building Services Piping applies to the following building services:
Condensing water Water for heating and cooling Steam and condensate Vacuum Compressed air and nontoxic nonflammable gases
The working pressure and temperature limits of B31.9 can be summarized to:
ASME B31.9 Building Services Piping - Working Pressure and Temperature Limits Service Temperature Limits Pressure Limits Steam and condensate maximum 366 oF (186 oC), minimum 0 oF (-18 oC) 150 psig (1000 kPa) Air, gases and vapors maximum 200 oF (93 oC), minimum 0 oF (-18 oC) 150 psig (1000 kPa) Nonflammable Liquids maximum 250 oF (121 oC), minimum 0 oF (-18 oC) 350 psig (2300 kPa) Related Topics Piping codes and standards - ASME, ANSI, ASTM, AGA, API, AWWA, BS, ISO, DIN and more.. Pressure ratings of pipes and tubes and their fittings - carbon steel , stainless steel, plastic, copper and more. Related Documents Pressure (psig) and temperature ratings for steel pipe flanges and flanged fittings ASME is one of the leading organizations in the world developing codes and standards. The ASME Performance Test Codes provide standard directions and rules for conducting and reporting tests. A survey of one of the most important pressure pipe codes - ASME B31, earlier known as ANSI B31. The working pressure and temperature limits of ASME Code B31.9 - Building Services Piping. The working pressure and temperature limits of ASME Code B31.9 - Building Services Piping. Maximum working pressure of carbon steel pipe at temperature 400 oF. Maximum temperature and pressure ratings of flanges conforming dimensions ASME B16.5 and materials specification ASTM A-105. Pressure (psig) and temperature (deg F) ratings for A-53 B and A-106 B, A333, A334 and API 5L carbon steel pipes - temperatures ranging 100 degF - 700 degF. Pressure (kPa)> and temperature (degC) ratings of ASTM A-106, API 5L and ASTM A-53 Seamless Carbon Steel Pipes - temperatures ranging -29 degC - 450 degC. Maximum operating and bursting pressures of CPVC - Chlorinated Poly (Vinyl Chloride) - piping systems. Commonly used standards for fiberglass pipes and their applications. Materials approved for gas pipes. Polyethylene pipe temperature and maximum operating pressure. Allowable wall stress in pipes according ASME M31.3. Maximum operating and required burst pressure of PVC - Polyvinyl Chloride - pipe fittings. Materials used in water distribution pipes. Water service pipe lines extends from the potable water source to the interior of buildings. Sizing water supply service and distribution lines based on Water Supply Fixture Units (WSFU). Search
Search is the most efficient way to navigate the Engineering ToolBox.
About the Engineering ToolBox!
We don't collect information from our users. More about
This page can be cited as
The Engineering ToolBox (2003). ASME B31.9 Building Services Piping - Working Pressure and Temperature Limits. [online] Available at: https://www.engineeringtoolbox.com/asme-b31-9-working-pressure-d_10.html [Accessed Day Month Year].
Modify the access date according your visit.