# Three-Phase Electrtical Motors - Power Factor vs. Inductive Load

The power factor of an AC electric power system is defined as the ratio ** active (true or real) power ** to ** apparent power **, where

**Active (Real or True) Power**is measured in watts (*W*) and is the power drawn by the electrical resistance of a system doing useful work**Apparent Power**is measured in volt-amperes*(VA)*and is the voltage on an AC system multiplied by all the current that flows in it. It is the vector sum of the**active**and the**reactive power****Reactive Power**is measured in volt-amperes reactive (*VAR*). Reactive Power is power stored in and discharged by inductive motors, transformers and solenoids

Reactive power is required for the magnetization of an electric motor but does not perform any work. Reactive power required by inductive loads increases the amounts of apparent power - and the required supply to the grid from the power supplier to the distribution system.

Increased reactive and apparent power will decrease the power factor - * PF *.

### Power Factor

It is common to define the Power Factor - * PF * - as the cosine of the phase angle between voltage and current - or the " * cosφ * ":

* PF = cos φ *

* where *

* PF = power factor *

* φ = phase angle between voltage and current *

The power factor defined by IEEE and IEC is the ratio between the applied ** active (true) power ** - and the ** apparent power **, and can in general be expressed as:

PF = P / S (1)

where

PF = power factor

P = active (true or real) power (Watts)

S = apparent power (VA, volts amps)

A low power factor is the result of inductive loads such as transformers and electric motors. Unlike resistance loads creating heat by consuming kilowatts, inductive loads require a current flow to create magnetic fields to produce the desired work.

Power factor is an important measurement in electrical AC systems because

- an overall power factor less than 1 indicates that the electricity supplier need to provide more generating capacity than actually required
- the current waveform distortion that contributes to reduced power factor is caused by voltage waveform distortion and overheating in the neutral cables of three-phase systems

International standards such as IEC 61000-3-2 have been established to control current waveform distortion by introducing limits for the amplitude of current harmonics.

#### Example - Power Factor

A industrial plant draws * 200 A * at * 400 V * and the supply transformer and backup UPS is rated * 400 V * x * 200 A = 80 kVA *.

If the power factor - * PF * - of the loads is * 0.7 * - only

80 kVA × 0.7

= 56 kW

of real power is consumed by the system. If the power factor is close to 1 (a purely resistive circuit) the supply system with transformers, cables, switch-gear and UPS could be made considerably smaller.

- Any power factor
*less than 1*means that the circuit's wiring has to carry more current than what would be necessary with zero reactance in the circuit to deliver the same amount of (true) power to the resistive load.

#### Conductor Cross-Section vs. Power Factor

Required cross-section area of conductor with lower power factor:

Power Factor |
1 | 0.9 | 0.8 | 0.7 | 0.6 | 0.5 | 0.4 | 0.3 |

Cross-Section |
1 | 1.2 | 1.6 | 2.04 | 2.8 | 4.0 | 6.3 | 11.1 |

A low power factor is expensive and inefficient and some utility companies may charge additional fees when the power factor is less than * 0.95 * . A low power factor will reduce the electrical system's distribution capacity by increasing the current flow and causing voltage drops.

### "Leading" or "Lagging" Power Factors

A Power Factor is usually stated as "leading" or "lagging" to show the sign of the phase angle.

- With a purely resistive load the current and voltage changes polarity in step and the power factor will be
*1*. Electrical energy flows in a single direction across the network in each cycle. - Inductive loads - transformers, motors and wound coils - consumes reactive power with current waveform lagging the voltage.
- Capacitive loads - capacitor banks or buried cables - generates reactive power with current phase leading the voltage.

Inductive and capacitive loads stores energy in magnetic or electric fields in the devices during parts of the AC cycles. The energy is returned back to the power source during the rest of the cycles.

In systems with mainly inductive loads - typically industrial plants with many electric motors - the lagging voltage are compensated with capacitor banks.

### Power Factor for a Three-Phase Motor

The total power required by an inductive device like a motor or similar consists of

- Active (true or real) power (measured in kilowatts, kW)
- Reactive power - the nonworking power caused by the magnetizing current, required to operate the device (measured in kilovars, kVAR)

The power factor for a three-phase electric motor can be expressed as:

PF = P / [(3)^{ 1/2 }U I] (2)

where

PF = power factor

P = power applied (W, watts)

U = voltage (V)

I = current (A, amps)

- or alternatively:

* P = (3) ^{ 1/2 } U I PF *

* = (3) ^{ 1/2 } U I cos φ (2b) *

U, l and cos * φ * are normally quoted on the motor nameplate.

### Typical Motor Power Factors

Power (hp) | Speed (rpm) | Power Factor (cos φ ) | ||||
---|---|---|---|---|---|---|

Unloaded | 1/4 load | 1/2 load | 3/4 load | full load | ||

0 - 5 | 1800 | 0.15 - 0.20 | 0.5 - 0.6 | 0.72 | 0.82 | 0.84 |

5 - 20 | 1800 | 0.15 - 0.20 | 0.5 - 0.6 | 0.74 | 0.84 | 0.86 |

20 - 100 | 1800 | 0.15 - 0.20 | 0.5 - 0.6 | 0.79 | 0.86 | 0.89 |

100 - 300 | 1800 | 0.15 - 0.20 | 0.5 - 0.6 | 0.81 | 0.88 | 0.91 |

*1 hp = 745.7 W*

### Power Factor by Industry

Typical un-improved power factors:

Industry | Power Factor |
---|---|

Brewery | 75 - 80 |

Cement | 75 - 80 |

Chemical | 65 - 75 |

Electro-chemical | 65 - 75 |

Foundry | 75 - 80 |

Forging | 70 - 80 |

Hospital | 75 - 80 |

Manufacturing, machines | 60 - 65 |

Manufacturing, paint | 65 - 70 |

Metalworking | 65 - 70 |

Mine, coal | 65 - 80 |

Office | 80 - 90 |

Oil pumping | 40 - 60 |

Plastic production | 75 - 80 |

Stamping | 60 - 70 |

Steel works | 65 - 80 |

Textiles | 35 - 60 |

### Benefits of Power Factor Corrections

- reduced power bills - avoiding low power factor penalty from the utility power company
- increased system capacity - additional loads can be added without overloading the system
- improved system operating characteristics by reduced line loss - due to less current
- improved system operating characteristics by gaining voltage - excessive voltage drops are avoided

### Power Factor Correction with Capacitor

Power factor before improvement (cosΦ) | Capacitor correction factor | ||||||||||
---|---|---|---|---|---|---|---|---|---|---|---|

Power factor after improvement (cosΦ) | |||||||||||

1.0 | 0.99 | 0.98 | 0.97 | 0.96 | 0.95 | 0.94 | 0.93 | 0.92 | 0.91 | 0.90 | |

0.50 | 1.73 | 1.59 | 1.53 | 1.48 | 1.44 | 1.40 | 1.37 | 1.34 | 1.30 | 1.28 | 1.25 |

0.55 | 1.52 | 1.38 | 1.32 | 1.28 | 1.23 | 1.19 | 1.16 | 1.12 | 1.09 | 1.06 | 1.04 |

0.60 | 1.33 | 1.19 | 1.13 | 1.08 | 1.04 | 1.01 | 0.97 | 0.94 | 0.91 | 0.88 | 0.85 |

0.65 | 1.17 | 1.03 | 0.97 | 0.92 | 0.88 | 0.84 | 0.81 | 0.77 | 0.74 | 0.71 | 0.69 |

0.70 | 1.02 | 0.88 | 0.81 | 0.77 | 0.73 | 0.69 | 0.66 | 0.62 | 0.59 | 0.56 | 0.54 |

0.75 | 0.88 | 0.74 | 0.67 | 0.63 | 0.58 | 0.55 | 0.52 | 0.49 | 0.45 | 0.43 | 0.40 |

0.80 | 0.75 | 0.61 | 0.54 | 0.50 | 0.46 | 0.42 | 0.39 | 0.35 | 0.32 | 0.29 | 0.27 |

0.85 | 0.62 | 0.48 | 0.42 | 0.37 | 0.33 | 0.29 | 0.26 | 0.22 | 0.19 | 0.16 | 0.14 |

0.90 | 0.48 | 0.34 | 0.28 | 0.23 | 0.19 | 0.16 | 0.12 | 0.09 | 0.06 | 0.02 | |

0.91 | 0.45 | 0.31 | 0.25 | 0.21 | 0.16 | 0.13 | 0.09 | 0.06 | 0.02 | ||

0.92 | 0.43 | 0.28 | 0.22 | 0.18 | 0.13 | 0.10 | 0.06 | 0.03 | |||

0.93 | 0.40 | 0.25 | 0.19 | 0.15 | 0.10 | 0.07 | 0.03 | ||||

0.94 | 0.36 | 0.22 | 0.16 | 0.11 | 0.07 | 0.04 | |||||

0.95 | 0.33 | 0.18 | 0.12 | 0.08 | 0.04 | ||||||

0.96 | 0.29 | 0.15 | 0.09 | 0.04 | |||||||

0.97 | 0.25 | 0.11 | 0.05 | ||||||||

0.98 | 0.20 | 0.06 | |||||||||

0.99 | 0.14 |

#### Example - Improving power factor with capacitor

An electrical motor with power * 150 kW * has power factor before improvement * cosΦ = 0.75 *.

For a required power factor after improvement * cosΦ = 0.96 * - the capacitor correction factor is * 0.58 *.

The required KVAR capacity can be calculated as

* C = (150 kW) 0.58 *

* = 87 KVAR *

### Suggested Capacitor Ratings for T-Frame NEMA Class B Motors

Recommended sizes of KVAR units needed for correction of induction motors to approximately 95% power factor.

Induction Motor Rating (HP) | Nominal Motor Speed (rpm) | |||||
---|---|---|---|---|---|---|

3600 | 1800 | 1200 | ||||

Capacitor Rating (KVAR) | Reduction of Line Current (%) | Capacitor Rating (KVAR) | Reduction of Line Current (%) | Capacitor Rating (KVAR) | Reduction of Line Current (%) | |

3 | 1.5 | 14 | 1.5 | 23 | 2.5 | 28 |

5 | 2 | 14 | 2.5 | 22 | 3 | 26 |

7.5 | 2.5 | 14 | 3 | 20 | 4 | 21 |

10 | 4 | 14 | 4 | 18 | 5 | 21 |

15 | 5 | 12 | 5 | 18 | 6 | 20 |

20 | 6 | 12 | 6 | 17 | 7.5 | 19 |

25 | 7.5 | 12 | 7.5 | 17 | 8 | 19 |

30 | 8 | 11 | 8 | 16 | 10 | 19 |

40 | 12 | 12 | 13 | 15 | 16 | 19 |

50 | 15 | 12 | 18 | 15 | 20 | 19 |

60 | 18 | 12 | 21 | 14 | 22.5 | 17 |

75 | 20 | 12 | 23 | 14 | 25 | 15 |

100 | 22.5 | 11 | 30 | 14 | 30 | 12 |

125 | 25 | 10 | 36 | 12 | 35 | 12 |

150 | 30 | 10 | 42 | 12 | 40 | 12 |

200 | 35 | 10 | 50 | 11 | 50 | 10 |

250 | 40 | 11 | 60 | 10 | 62.5 | 10 |

300 | 45 | 11 | 68 | 10 | 75 | 12 |

350 | 50 | 12 | 75 | 8 | 90 | 12 |

400 | 75 | 10 | 80 | 8 | 100 | 12 |

450 | 80 | 8 | 90 | 8 | 120 | 10 |

500 | 100 | 8 | 120 | 9 | 150 | 12 |

## Related Topics

### • Electrical

Electrical engineering with units, amps and electrical wiring. Wire gauges, electrical formulas, motors and more.

## Related Documents

### AC - Active, Reactive and Apparent Power

Real, imaginary and apparent power in AC circuits.

### AC Circuits - Power vs. Voltage and Current

The alternating current In an AC circuit is generated by a sinusoidal voltage source.

### Aluminum Conductor Characteristics

Characteristics of all-aluminum conductors (AAC).

### Asynchronous Induction Motors - Electrical Properties

Typical electrical motor data like nominal current, fuse, start ampere, size of contactor and circuit breaker - for asynchronous induction motors.

### Electric Motor Calculator

Calculate amps, hp and kVA for electrical motors.

### Electric Motors - 480 Volt Wiring

480V electrical motor wiring data - NEMA amps, starter size, HMCP size for motors ranging 1/2 to 500 hp.

### Electrical Induction Motors - Slip

Slip is the difference between an electrical induction motor's synchronous and asynchronous speed.

### Electrical Motors - Frame Dimensions

Electrical motors NEMA frame dimensions.

### Electrical Motors - Heat Loss

Heat loss from an electrical motor to the surroundings.

### Electrical Motors - Insulation Classes

Electrical motors NEMA temperature and insulation classes.

### Electrical Motors - Locked Rotor Design Code Letters

NEMA locked rotor indicating code letters for electrical motors.

### Electrical Motors - Service Factors

Service factor - *SF* - is a measure of periodically overload capacity at which a motor can operate without beeing damaged.

### Electrical Motors - Speed at Operating vs. Synchronous Load

Speed of an operating electrical motor with load is lower than the synchronous speed (no load) of the motor.

### Electrical Motors - Speed vs. No. of Poles and Frequency

The speed of electrical motors with 2, 4, 6 or 8 poles at 50 Hz and 60 Hz.

### Electrical Motors - Starting Devices

Direct-on-line starters, star-delta starters, frequency drives and soft starters.

### Electrotechnical Abbreviations

Abbreviations according the International Electrotechnical Commission (IEC).

### Heat Gain from Electrical Motors in Continuous Operation

Amount of heat transferred from electrical motor to ambient room vs. locations of fan and motor.

### IEC Electric Motor Duty Cycles

The eight - S1 - S8 - IEC duty cycles of operating electrical motors.

### Induction Motors - No. of Poles and Synchronous vs. Full Load Speed

Synchronous and full load speed of amplitude current (AC) induction motors.

### Law of Cosines

One side of a triangle when the opposite angle and two sides are known.

### Polyphase Motors - Voltage Imbalance vs. Derating Factor

Increased voltage imbalance and decreased efficiency.

### Power

Power is the rate at which work is done or energy converted.

### Single Phase Power Equations

Power equations for single phased electrical systems.

### Three-Phase Electrical Motors - Power vs. Amps and Voltage

Full load amps, wire and conduit sizes for three phase electrical motors.

### Three-Phase Power - Equations

Electrical 3-phase equations.