# Transmission Heat Loss through Building Elements

The heat transmission through a building wall or similar construction can be expressed as:

H_{t}= U A dt (1)

where

H_{t}= heat flow (Btu/hr, W, J/s)

U = overall heat transfer coefficient, "U-value" (Btu/hr ft^{2}^{o}F, W/m^{2}K)

A = wall area (ft^{2}, m^{2})

dt = temperature difference (^{o}F, K)

The overall heat transfer coefficient - the U-value - describes how well a building element conducts heat or the rate of transfer of heat (in watts or Btu/hr) through one unit area (m^{2} or ft^{2}) of a structure divided by the difference in temperature across the structure.

### Online Heat Loss Calculator

### Common Heat Transfer Coefficients of some common Building Elements

Building Element | Heat-Transfer Coefficient U-value | ||
---|---|---|---|

(Btu/(hr ft^{2} ^{o}F)) | (W/(m^{2}K)) | ||

Doors | Single sheet - metal | 1.2 | 6.8 |

1 inch - wood | 0.65 | 3.7 | |

2 inches - wood | 0.45 | 2.6 | |

Roofing | Corrugated metal - uninsulated | 1.5 | 8.5 |

1 inch wood - uninsulated | 0.5 | 2.8 | |

2 inches wood - un-insulated | 0.3 | 1.7 | |

1 inch wood - 1 inch insulation | 0.2 | 1.1 | |

2 inch wood - 1 inch insulation | 0.15 | 0.9 | |

2 inches - concrete slab | 0.3 | 1.7 | |

2 inches - concrete slab - 1 inch insulation | 0.15 | 0.9 | |

Windows | Vertical single glazed window in metal frame | 5.8 | |

Vertical single glazed window in wooden frame | 4.7 | ||

Vertical double glazed window, distance between glasses 30 - 60 mm | 2.8 | ||

Vertical triple glazed window, distance between glasses 30 - 60 mm | 1.85 | ||

Vertical sealed double glazed window, distance between glasses 20 mm | 3.0 | ||

Vertical sealed triple glazed window, distance between glasses 20 mm | 1.9 | ||

Vertical sealed double glazed window with "Low-E" coatings | 0.32 | 1.8 | |

Vertical double glazed window with "Low-E" coatings and heavy gas filling | 0.27 | 1.5 | |

Vertical double glazed window with 3 plastic films ("Low-E" coated) and heavy gas filling | 0.06 | 0.35 | |

Horizontal single glass | 1.4 | 7.9 | |

Walls | 6 inches (150 mm) - poured concrete 80 lb/ft^{3} |
0.7 | 3.9 |

10 inches (250 mm) - brick | 0.36 | 2.0 |

### U and R-values

U-value (or U-factor) is a measure of the rate of heat loss or gain through a construction of materials. The lower the U-factor, the greater the material's resistance to heat flow and the better is the insulating value. U-value is the inverse of R-value.

The overall U-value of a construction consisting of several layers can be expressed as

U = 1 / ∑ R (2)

where

U = heat transfer coefficient (Btu/hr ft^{2}^{o}F, W/m^{2}K)

R = "R-value" - the resistance to heat flow in each layer (hr ft^{2}^{o}F/Btu, m^{2}K/W)

The R-value of the single layer can be expressed as:

R = 1 / C = s / k (3)

where

C = layer conductance (Btu/hr ft^{2}^{o}F, W/m^{2}K)

k = thermal conductivity of layer material (Btu in/hr ft^{2}^{o}F, W/mK)

s = thickness of layer (inches, m)

Note! - in addition to resistance in each construction layer - there is a resistance from the inner and outer surface to the surroundings. If you want to add the surface resistance to the *U* calculator below - use one - *1*- for thickness - *l*_{t} - and the surface resistance for the conductivity - *K*.

### Online *U value* Calculator

This calculator can be used to calculate the overall U-value for a construction with four layers. Add the thickness - *l _{t}* - and the layer conductivity -

*K*- for each layer. For fewer than four layers, replace the thickness of one or more layers with zero.

### Example - U value Concrete Wall

A concrete wall with thickness* 0.25 (m)* and conductivity *1.7 (W/mK)* is used for the default values in the calculator above. The inside and outside surface resistance is estimated to *5.8 (m ^{2}K/W)*.

The U value can be calculated as

*U = 1 / (1 / (5.8 m ^{2}K/W) + (0.25 m) / (1.7 W/mK)) *

* = 3.13 W/m ^{2}K*

### R-values of Some Common Building Materials

Material | Resistance R-value | |
---|---|---|

(hr ft^{2} ^{o}F/Btu) | (m^{2}K/W) | |

Wood bevel siding 1/2" x 8", lapped | 0.81 | 0.14 |

Wood bevel siding 3/4" x 10", lapped | 1.05 | 0.18 |

Stucco (per inch) | 0.20 | 0.035 |

Building paper | 0.06 | 0.01 |

Plywood 1/4" | 0.31 | 0.05 |

Plywood 3/8" | 0.47 | 0.08 |

Plywood 1/2" | 0.62 | 0.11 |

Hardboard 1/4" | 0.18 | 0.03 |

Softboard, pine or similar 3/4" | 0.94 | 0.17 |

Softboard, pine or similar 1 1/2" | 1.89 | 0.33 |

Softboard, pine or similar 2 1/2" | 3.12 | 0.55 |

Gypsum board 1/2" | 0.45 | 0.08 |

Gypsum board 5/8" | 0.56 | 0.1 |

Fiberglass 2" | 7 | 1.2 |

Fiberglass 6" | 19 | 3.3 |

Common brick per inch | 0.20 | 0.04 |

### R-values of Some Common Wall Constructions

Material | Resistance R-value | |
---|---|---|

(hr ft^{2} ^{o}F/Btu) | (m^{2}K/W) | |

2 x 4 stud wall, uninsulated | 5 | 0.88 |

2 x 4 stud wall with 3 1/2" batt insulation | 15 | 2.6 |

2 x 4 stud wall with 1" polystyrene rigid board, 3 1/2" insulation blanket | 18 | 3.2 |

2 x 4 stud wall with 3/4" insulation board, 3 1/2" batt insulation, 5/8" polyurethane insulation | 22 | 3.9 |

2 x 6 stud wall with 5 1/2" insulation blanket | 23 | 4 |

2 x 6 stud wall with 3/4" insulation board, 5 1/2" batt insulation, 5/8" polyurethane insulation | 28 | 4.9 |

## Related Topics

### • Heating Systems

Design of heating systems - capacities and design of boilers, pipelines, heat exchangers, expansion systems and more.

## Related Documents

### Arithmetic and Logarithmic Mean Temperature Difference

Arithmetic Mean Temperature Difference in Heat Exchangers - *AMTD* - and Logarithmic Mean Temperature Difference - *LMTD* - formulas with examples - Online Mean Temperature Calculator.

### Building Elements - Heat Loss vs. Thermal Resistivity

Thermal resistance in building elements like walls, floors and roofs above and below the ground.

### Duct Wrap Insulation - Thermal Resistance

Heat flow thermal resistance of unfaced and faced duct wrap insulation.

### Heat Loss from Buildings

Overall heat transfer loss from buildings - transmission, ventilation and infiltration.

### Heat Transfer Coefficients in Heat Exchanger Surface Combinations

Average overall heat transmission coefficients for fluid and surface combinations like Water to Air, Water to Water, Air to Air, Steam to Water and more.

### Heating Systems - Steam and Condensate Loads

Calculating steam and condensate loads in steam heated systems.

### Infiltration - Heat Losses from Buildings

Estimated infiltration heat losses from buildings.

### Polyurethane Insulation

Thermal conductivity - k-values - vs. temperature.

### Roof Framing

Run, roof slope, gable height and gable area.

### Steam Radiators and Convectors - Heating Capacities

Steam radiators and steam convectors - heating capacities and temperature coefficients.

### Walls - No. of Studs

Calculate required number of studs in a wall.

### Water - Thermal Conductivity vs. Temperature

Figures and tables showing thermal conductivity of water (liquid and gas phase) with varying temperature and pressure, SI and Imperial units.

### Windows - Inside Condensation

Water condensation on inside glass windows surfaces vs. outside temperature and inside temperature and humidity.