# Air Ducts - Major Friction Head Loss, Online Calculator

The major loss, or friction loss, in a circular duct in galvanized steel with turbulent flow can for imperial units be expressed

Δh = 0.109136 q^{ 1.9 }/ d_{ e }^{ 5.02 }(1)

where

Δh = friction or head loss (inches water gauge/100 ft of duct)

d_{ e }= equivalent duct diameter (inches)

q = air volume flow - (cfm - cubic feet per minute)

For rectangular ducts the equivalent diameter must be calculated.

### Air Ducts Friction Loss Calculator - Imperial Units

The head loss calculator below is based on formula * (1) * :

Head loss and air flow velocity for some common duct sizes and air flow volumes can be taken from the table below:

Air Volume (cfm) | Head Loss (inches water gauge per 100 feet duct) | ||||||
---|---|---|---|---|---|---|---|

Air velocity (ft/min) | |||||||

Duct Size (inches) | |||||||

4 | 5 | 6 | 8 | 10 | 12 | 16 | |

100 | 0.65 | 0.21 | 0.09 | 0.02 | 0.01 | ||

1146 | 733 | 509 | 286 | 183 | |||

200 | 0.8 | 0.32 | 0.08 | 0.02 | 0.01 | ||

1467 | 1019 | 573 | 367 | 255 | |||

400 | 1.19 | 0.28 | 0.09 | 0.04 | 0.01 | ||

2037 | 1146 | 733 | 509 | 286 | |||

800 | 0.34 | 0.14 | 0.03 | ||||

1467 | 1019 | 573 | |||||

1600 | 0.12 | ||||||

1146 |

Air velocity should not exceed certain limits to avoid unacceptable noise generation.

### Air Ducts Friction Loss Calculator - SI Units

This pressure loss calculator is based on formula * (1) * with input and output values modified for SI units.

### Air Ducts - Velocity and Friction Loss - Excel Template

This Excel template can be used to calculate velocity and friction loss in air ducts.

### Air Ducts - Friction Loss Diagram

The chart below can be used to estimate friction loss in air ducts.

The default values are for air flow * 400 cfm (680 m ^{3} /h) *, duct size

*8 in (200 mm)*and friction loss

*0.28 inH2O/100ft (2.3 Pa/m)*.

## Related Topics

### • Ventilation Systems

Design of systems for ventilation and air handling - air change rates, ducts and pressure drops, charts and diagrams and more.

## Related Documents

### Air Duct Velocities

Typical air duct velocities in applications like ventilation systems or compressed air systems.

### Air Ducts - Friction Loss Diagram

A major friction loss diagram for air ducts - Imperial units ranging *10 - 100 000 cfm*.

### Air Ducts - Friction Loss Diagram

A major friction loss diagram for air ducts - SI units.

### Air Ducts - Velocity Diagram

Air flow volume, duct size, velocity and dynamic pressure.

### Duct Sizing - the Equal Friction Method

The equal friction method for sizing air ducts is easy and straightforward to use.

### Duct Systems - Pressure Classifications

Duct systems are commonly divided into three pressure classifications.

### Duct Velocity

Calculate velocities in circular and rectangular ducts - imperial and SI-units - online calculator.

### Ducts Sizing - the Velocity Reduction Method

The velocity reduction method can be used when sizing air ducts.

### Ductwork - Seal Classes

Ductwork air leakage classes.

### Equivalent Diameter - Rectangular vs. Circular HVAC Ducts

Rectangular equivalent diameter for air flows between *100 - 50000 cfm*.

### Fluid Flow - Equivalent Diameter

Convert rectangular and oval duct geometry to a equivalent circular diameter - online calculator with imperial and SI-units.

### Fluid Flow - Hydraulic Diameter

Calculate hydraulic diameter for pipes and ducts.

### Sizing Circular Ducts

A rough guide to maximum air volume capacity of circular ducts in comfort, industrial and high speed ventilation systems.

### Spiral Ducts - Dimensions

Standard dimensions of spiral ducts - Imperial units.

### Velocity Classification of Ventilation Ducts

Recommended air velocities in ventilation ducts