Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

# Equivalent Diameter - Rectangular vs. Circular HVAC Ducts

## Rectangular equivalent diameter for air flows between 100 - 50000 cfm.

The equivalent diameter is the diameter of a circular duct or pipe that gives the same pressure loss as an equivalent rectangular duct or pipe.

The table below can be used to compare equivalent diameters for rectangular and round circular ducts. The table is based on the ducts friction loss formula.

The rectangular dimensions and the air flow volume are adapted to the equal friction loss method of sizing ventilation duct systems.

The table below indicates maximum air flow in low and medium pressure loss ducts.

• maximum friction < 0.1 - 0.2 inches W.G./100 ft
• air velocity < 1500 - 2000 ft/min (8 - 10 m/s)

Customized values can be calculated in the top row.

Air flow
- q -
(Cubic Feet per Minute, cfm)
(m3/s)
Rectangular Duct Sizes
(inches)
(mm) x (mm)
Equivalent Diameter
Round Duct Sizes
- de -
(inches)
(mm)
Velocity in equivalent round Duct
- v -
(ft/min)
(m/s)
Friction Loss
(inH2O / 100 ft duct)
(Pa/100m)

()
x
() x ()

()

()

()
80
(0.04)
3 x 7
4 x 5
4.9
4.9
611
(3.1)
0.15
100
(0.045)
4 x 6 5.33 646
(3.28)
0.16
120
(0.05)
4 x 7
5 x 6
5.7
6.0
670
(3.57)
0.15
140
(0.063)
4 x 8 6.09 691
(3.5)
0.15
150
(0.068)
3.5 x 10 6.26 702
(3.6)
0.15
160
(0.07)
4 x 9
5 x 7
6 x 6
6.4
6.4
6.6
710
(3.6)
0.15
180
(0.08)
4 x 10 6.74 726
(3.69)
0.15
200
(0.09)
6 x 7 7.1 732
(3.7)
0.14
230
(0.12)
4 x 12 7.31 790
(4.01)
0.15
250
(0.11)
6 x 8 7.55 803
(4.08)
0.15
270
(0.1)
4 x 14 7.81 811
(4.12)
0.15
300
(0.14)
5 x 12
6 x 10
7 x 8
8.3
8.4
8.2
804
(4.1)
0.14
400
(0.18)
7 x 10
8 x 9
9.1
9.3
884
(4.5)
0.15

480
(0.22)

8 x 10
9 x 9
9.8
9.8
923
(4.7)
0.15
600
(0.27)
8 x 12
10 x 10
10.7
10.9
909
(4.9)
0.14
750
(0.34)
8 x 14
9 x 12
10 x 11
11.5
11.3
11.5
1047
(5.3)
0.15
800
(0.36)
8 x 15
10 x 12
11.8
12.0
1048
(5.3)
0.15
1000
(0.45)
10 x 14
12 x 12
12.9
13.1
1104
(5.6)
0.15
1300
(0.59)
12 x 14 14.1 1189
(6.0)
0.15
1400
(0.63)
12 x 15 14.6 1197
(6.1)
0.15
1700
(0.77)
10 x 22
14 x 15
15.9
15.8
1231
(6.3)
0.14
1900
(0.86)
12 x 19
14 x 16
16.4
16.4
1295
(6.6)
0.15
2000
(0.9)
10 x 25
12 x 20
15 x 16
16.9
16.8
16.9
1291
(6.6)
0.14
2500
(1.13)
14 x 20
15 x 18
18.2
17.9
1381
(7.0)
0.15
2800
(1.26)
12 x 26
16 x 20
19.0
19.5
1428
(7.3)
0.15
3300
(1.49)
12 x 30
14 x 25
20.2
20.2
1480
(7.5)
0.15
3800
(1.71)
12 x 34
15 x 25
21.4
21.0
1525
(7.8)
0.15
4100
(1.84)
12 x 36
16 x 25
20 x 20
21.9
21.7
21.9
1565
(8.0)
0.15
5400
(2.43)
12 x 45
16 x 30
20 x 24
24.1
23.7
23.9
1699
(8.6)
0.15
6200
(2.79)
16 x 36
18 x 30
23 x 25
24.7
25.2
26.2
1719
(8.7)
0.15
7200
(3.24)
16 x 40
20 x 32
25 x 25
27.0
27.5
27.3
1816
(9.2)
0.15
8400
(3.78)
20 x 35
25 x 28
28.6
28.9
1879
(9.5)
0.15
10300
(4.64)
16 x 55
20 x 43
25 x 38
31.0
31.5
33.5
1964
(10.0)
0.15
13000
(5.85)
20 x 50
30 x 32
33.7
33.9
2098
(10.7)
0.15
13500
(6.08)
20 x 55
30 x 35
35.2
35.4
2002
(10.2)
0.13
15000
(6.75)
25 x 48
30 x 40
37.4
37.8
1969
(10)
0.12
17000
(7.65)
32 x 40 39.1 2044
(10.4)
0.12
19000
(8.55)
32 x 45
35 x 40
41.3
40.9
2039
(10.4)
0.11
• 1 in = 25.4 mm
• 1 inH2O / 100 ft = 84 mmH2O /100 m

Note! - due to larger circumference and more friction area related to air volume - a circular duct is always more efficient than a rectangular duct.

### Example - Air Flow in Rectangular vs. Circular Duct

2000 cfm (0.94 m3/s) of air flows through a 10 x 12 inches rectangular duct.

The friction loss according the table above is 0.81 inches water gauge per 100 ft duct (aprox. 6.6 Pa/m).

The velocity in the rectangular duct is

v = (2000 cfm) / (((10 inches) (1/12 ft/inches) ((12 inches)(1/12 ft/inches)))

= 2400 ft/min  (12.2 m/s)

The velocity in the the equivalent 12 inch circular duct according the table above is 2589 ft/min (13.2 m/s).

## Related Topics

• Air Conditioning - Air Conditioning systems - heating, cooling and dehumidification of indoor air for thermal comfort.
• Ventilation - Systems for ventilation and air handling - air change rates, ducts and pressure drops, charts and diagrams and more.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

## Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.

Temperature

oC
oF

Length

m
km
in
ft
yards
miles
naut miles

Area

m2
km2
in2
ft2
miles2
acres

Volume

m3
liters
in3
ft3
us gal

Weight

kgf
N
lbf

Velocity

m/s
km/h
ft/min
ft/s
mph
knots

Pressure

Pa (N/m2)
bar
mm H2O
kg/cm2
psi
inches H2O

Flow

m3/s
m3/h
US gpm
cfm

6 24