Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

Equivalent Length Method - Calculating Minor Pressure Loss in Piping Systems

Pressure loss in piping systems by using the Equivalent Pipe Length Method

An efficient and simple way to calculate the pressure loss in a piping system is the "Equivalent Pipe Length Method".

1. Make a Diagram of the Piping System

Make a diagram where the system is structured with nodes as shown below. In the very simply circulating system used in this example the first node (0) is the pump. The next node is the tees (2) where the piping system splits up. The other nodes are the heating radiators.

In many systems the structure can be simplified as above since the piping in both directions are of same size. If a more fine grained approach is required, additional nodes can be added in both directions as shown below. 2. Make a calculation table

With the most simplified nodes structure above a calculation table can be made as shown below. Each section from node to node is calculated by supplying length, volume flow, pipe size, pressure loss from diagrams or tables for the actual pipes and components in the sections and their individual equivalent length substituting the the minor loss. An excel template with the table above can be downloaded here:

Note! The flow and pressure units must be adjusted to the data available for your piping system.

3. Add Volume flow, Pipe Size and Pressure Loss for each Section

Add actual pipe size and in each section. Use tabulated data or a diagrams.

The pressure loss may alternatively be calculated with the Hazen-Williams Equation or the Darcy-Weisbach Formula.

• Pressure loss for many types of pipes can be found here.

4. Add Equivalent Length of all Valves, Fittings and Straight Pipes

Add the equivalent length of all valves, components, fittings and straight pipes in the sections.

5. Summarize the Pressure Loss in each Section

Calculate and summarize the pressure loss in each section.

6. Summarize the Pressure Loss in all Paths

Finally, add up the pressure loss in all sections that form unique paths. In the example above there are two unique paths - one is section 0 - 2 - 3, the other is section 0 - 2 - 4. Add extra columns for additional paths in more complicated systems.

The highest pressure loss determines the pump head.

7. Add Balancing Valves

Add valves where it is necessary to balance the system. In the example above a balancing valve is added in section 2-4.

Note! The Equivalent Pipe Length Method can be adapted to most piping systems - like water supply systems, gravity heating systems and similar.

Related Topics

• Heating - Heating systems - capacity and design of boilers, pipelines, heat exchangers, expansion systems and more
• Design Strategies - Piping systems and design strategies - documentation, P&ID, flow diagrams - capacities and limits
• Fluid Flow and Pressure Drop - Pipe lines - fluid flow and pressure loss - water, sewer, steel pipes, pvc pipes, copper tubes and more

Tag Search

• en: equivalent length method pressure head loss minor

Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro .Add the Engineering ToolBox extension to your SketchUp from the SketchUp Pro Sketchup Extension Warehouse!

About the Engineering ToolBox!

Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.

Citation

• Engineering ToolBox, (2004). Equivalent Length Method - Calculating Minor Pressure Loss in Piping Systems. [online] Available at: https://www.engineeringtoolbox.com/equivalent-pipe-length-method-d_804.html [Accessed Day Mo. Year].

Modify access date.

. .

Scientific Online Calculator 10 11