Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

# Room Sensible Heat Factor - RSHF

The Room Sensible Heat Factor - RSHF - expresses the ratio between sensible heat load and total heat load in a room. It can be expressed as:

RSHF = Qsr / Qtr                           (1)

where

RSHF = room sensible heat factor

Qsr = sensible heat load in room (kW, Btu/hr)

Qtr = total heat load in room (kW, Btu/hr)

(1) can be modified to:

RSHF = cp (tr - ti) / (hr - hi)                                 (2)

where

cp = specific heat air (kJ/kg.oC)

tr = room temperature (oC)

ti = inlet temperature (oC)

hr = room enthalpy (kJ/kg)

hi = inlet enthalpy (kJ/kg)

### Example - Room Sensible Heat Factor - RSHF

The sensible heat generated within a room is 4 kW. The latent heat generated is 1.4 kW.

The Room Sensible Heat Factor can be calculated as:

RSHF = (4 kW) / ((4 kW) + (1.4 kW))

= 0.75

## Related Topics

### • Air Psychrometrics

Moist and humid air calculations. Psychrometric charts and Mollier diagrams. Air-condition systems temperatures, absolute and relative humidities and moisture content in air.

## Related Documents

### Air - Thermophysical Properties

Thermal properties of air at different temperatures - density, viscosity, critical temperature and pressure, triple point, enthalpi and entropi, thermal conductivity and diffusivity and more.

### Cooling and Heating Equations

Latent and sensible cooling and heating equations - imperial units.

### Cooling Load - Latent and Sensible Heat

Latent and sensible cooling loads to consider when designing HVAC systems.

### Great Sensible Heat Factor - GSHF

The Great Sensible Heat Factor is the ratio sensible to total heat in a cooling coil.

### Heat Index

Equivalent heat index vs. air temperature and relative humidity - in degrees Fahrenheit and Celsius.

### Human Heat Gain

Heat gain from persons in air conditioned spaces - in btu/hr.

### Indoor Relative Humidity vs. Outdoor Relative Humidity and Temperature

Recommended indoor relative humidity vs. outdoor relative humidity and temperature.

### Latent Heat Flow

Latent heat is the heat when supplied to or removed from air results in a change in moisture content - the temperature of the air is not changed.

### Metabolic Heat Gain from Persons

Human metabolic heat gain in air conditioned rooms.

### Sensible Heat Flow

Sensible heat is dry heat causing change in temperature but not in moisture content

### Sensible Heat Ratio - SHR

The ratio Sensible Heat (or Cooling) Load to the Total Heat (or Cooling) Load.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

## Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.