The fluid flow velocities in water systems should not exceed certain limits to avoid noise and damaging wear and tear of pipes and fittings. The table below can be used as a guide to maximum velocities:
|General Water Service||0.9 - 2.4||3 - 8|
|Tap water (low noise)||0.5 - 0.7||1.6 - 2.3|
|Tap water||1.0 - 2.5||3.3 - 8.2|
|Cooling water||1.5 - 2.5||4.9 - 8.2|
|Suction boiler feed water||0.5 - 1.0||1.6 - 3.3|
|Discharge boiler feed water||1.5 - 2.5||4.9 - 8.2|
|Condensate||1.0 - 2.0||3.3 - 6.5|
|Process water||1.5 - 3||5 - 10|
|Pump discharge||1.5 - 3||5 - 10|
|Pump suction||0.9 - 2.4||3 - 8|
|Heating circulation||1.0 - 3.0||3.3 - 9.8|
Hot and cold water service systems - design properties, capacities, sizing and more.
Recommended max suction flow velocity when pumping boiling fluids.
Recommended max flow velocity on the delivery (pressure) side when pumping boiling liquids.
Sizing cooling water pipe lines - maximum allowable flow, velocity and pressure drops.
Design procedures for domestic hot water service systems.
ABMA recommended feed water chemistry limits for steam boilers.
Free online design tool for designing hot water heating systems - metric units.
Online design tool for hot water heating systems.
Discharge length vs. volume flow from water filled horizontal pipes.
Typical fluid flow velocities for common liquids, gases and vapors.
Calculate fluid velocity and volume flow in pipes and tubes.
Friction loss (psi/100 ft) and velocity for water flow in plastic PVC pipe schedule 40.
Volume flow and discharge height from vertical water pipes.
Recommended max. flow velocities on delivery sides of pumps in viscous systems.
Recommended maximum flow velocities in water systems on the delivery side of the pump.
Sizing of water supply pipe lines.
Free online tool for designing water supply systems in buildings.