hfe = 2258 kJ/kg, enthalpy of evaporation at 1 bar abs
The flash steam generated can be calculated as
w% = 100 ((781 kJ/kg) - (418 kJ/kg)) / (2258 kJ/kg)
= 16.1 %
If the steam flow rate through the heat exchanger is 200 kg/h - the condensate load can be calculated as
wc = (200 kg/h) (16.1 %) / 100
= 32 kg/h
Flash steam generation - thermodynamic fundamentals, heat loss, energy recovery and more.
Sizing of steam and condensate pipe lines - pressure loss, recommended velocity, capacity and more.
Maximum capacities for condensate pipe lines in kW steam consumption.
When condensate leaves the steam traps - flash steam is generated. Amount of flash steam generated at different pressures - kN/m2.
Saturated Steam Table with steam properties as specific volume, density, specific enthalpy and specific entropy.
Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!
We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.
Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.
If you want to promote your products or services in the Engineering ToolBox - please use Google Adwords. You can target the Engineering ToolBox by using AdWords Managed Placements.