Dimensions of CTS - Copper Tube Sized CPVC (Chlorinated Poly Vinyl Chloride) tubes
CTS (Copper Tube Size) and CPVC1) (Chlorinated Poly Vinyl Chloride) tubes according ASTM D2846 Standard Specification for Chlorinated Poly(Vinyl Chloride) (CPVC) Plastic Hot- and Cold-Water Distribution Systems:
|Size Nominal |
|Outside Diameter |
|Wall Thickness |
|Aprox. Weight |
|½||0.625||0.060 - 0.080||0.085|
|¾||0.875||0.080 - 0.100||0.140|
|1||1.125||0.102 - 0.122||0.218|
|1¼||1.375||0.125 - 0.145||0.330|
|1½||1.625||0.148 - 0.168||0.460|
|2||2.125||0.193 - 0.216||0.790|
1) Chlorinated Poly Vinyl Chloride (CPVC) is a thermoplastic pipe and fitting material made with CPVC compounds meeting the requirements of ASTM Class 23447 as defined in ASTM D1784 Standard Specification for Rigid Poly(Vinyl Chloride) (PVC) Compounds and Chlorinated Poly(Vinyl Chloride) (CPVC) Compounds.
CPVC applications are for potable water distribution, corrosive fluid handling in industry, and fire suppression systems.
- 1 inch = 25.4 mm
- PVC and CPVC Pipes - Schedule 40 & 80 according ASTM D1785 Standard Specification for Poly(Vinyl Chloride) (PVC) Plastic Pipe, Schedules 40, 80, and 120