Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

# Condensate Pumping

## High temperatures and danger of impeller cavitation is the major challenge for condensate pumping in steam systems.

Often its necessary to pump condensate generated in heat exchangers and other consumers widely distributed in a plant, back to the condensate receiver in the boiler house. A special challenge with hot condensate, which is often close to 212oF (100oC), is cavitation of the pump and the pump impeller.

Centrifugal pumps generates lower pressure behind the wheels and the hot condensate temporarily evaporates and expands on the back side of the vanes - before it implodes and condensates. Over time this erodes and destroys the pump impeller.

To avoid the problem there are two alternative solutions:

• Add pressure to the suction side of the pump
• Use a pressure powered pump instead of a centrifugal pump

### Add Pressure to the Suction Side of the Pump

If the absolute pressure exceeds the vapor pressure at the actual temperature of the fluid entering the pump, then the Net Positive Suction Head (NPSH) is positive and its possible to avoid cavitation.

A NPSH above the manufacturers specification is important to avoid that water start boiling behind the impeller. The NPSH can be expressed as:

NSPH = 144 / ρ(pa - pvp) + hs - hf                                        (1)

where

ρ = density of water at the appropriate temperature (lb/ft3)

pa = absolute pressure in the condensate receiver supplying the condensate pump. This is the same as atmospheric pressure if the receiver is vented (psi)

pvp = absolute evaporation pressure of condensate at the liquid temperature (psi)

hs = total suction head in feet. Positive for a head above the pump and negative for a lift to the pump.

hf = friction loss in the suction piping

According to (1) the NPSH can be increased by

• increasing the difference in the pressure in the receiver and the condensate pressure, and/or
• extend the static difference hs by lifting the receiver or lowering the pump, and/or
• increasing the piping dimensions for minimizing the friction loss hf in the suction pipe

If it's not possible to increase the suction pipe and lowering the pump under the receiver it may be possible to reduce the absolute evaporation pressure in the condensate Pvp by reducing the condensate temperature with a cooling exchanger in the suction pipe.

### Use a Pressure Powered Pump

A pressure powered pump use steam or air pressure to push the condensate from the receiver back to the boiler room. In principle its a simple intermittent mechanical construction working in cycle where a receiver in the pump is filled with condensate before steam or pressurized air pushes the condensate out and back to the boiler room.

External power is not required since available steam or pressurized air are used as power. There is no danger for cavitation.

### Other Liquids as LPG

The pumping of other boiling liquids - like LPG (-43oC in normal atmospheric pressure) - offers the same challenges to manufactures and users. LPG is stored at exactly its boiling point (at the actual pressure in the tank) and any increase of temperature, as well as any decrease in pressure, will cause the product to boil and form vapor. In many installations, the suction friction head is equal or larger than the static suction head, making the available NPSH a negative value. The pressure drop due to the flow restrictions in the inlet piping system, e.g., excess flow valve, control valves, fittings, strainer, etc., will induce the LPG vapor formation at the pumps suction port.

## Related Topics

• Steam and Condensate - Steam & condensate systems- properties, capacities, pipe sizing, systems configuration and more.
• Pumps - Piping systems and pumps - centrifugal pumps, displacement pumps - cavitation, viscosity, head and pressure, power consumption and more.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

## Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.

Temperature

oC
oF

Length

m
km
in
ft
yards
miles
naut miles

Area

m2
km2
in2
ft2
miles2
acres

Volume

m3
liters
in3
ft3
us gal

Weight

kgf
N
lbf

Velocity

m/s
km/h
ft/min
ft/s
mph
knots

Pressure

Pa (N/m2)
bar
mm H2O
kg/cm2
psi
inches H2O

Flow

m3/s
m3/h
US gpm
cfm

6 24