Pressure drop in psi per 100 ft compressed air pipeline can be estimated for some typical entering pressures in the diagrams below. The diagrams are calculated for schedule 40 pipes.
Other dimensions or pressures can be calculated with the
Applied Pressure 50 psig
- 1 ft (foot) = 0.3048 m
- 1 cfm = 1.7 m3/h = 0.028 m3/min
- 1 psi = 0.069 bar = 0.070 kg/cm2
Applied Pressure 100 psig
Applied Pressure 150 psig
The SCFM - Standard Cubic Feet per Minute - determines the weight of air to fixed or "Standard" conditions. There are several definitions of SCFM. The most commonly used in the United States is based on the properties
- 14.696 Pounds per Square Inch (psia)
- 60 Degrees Fahrenheit (oF)
- 0% Relative Humidity (RH)
Europeans normally use one ATA and 0oC as SCFM.
Compressed Air Pipe Line Pressure Loss other Dimensions
Compressed air pressure drop in pipes with other dimensions than schedule 40 can be calculated from
dp = dp40 (d40 / d)5 (1)
dp = actual pressure drop (psi per 100 ft pipe)
dp40 = pressure drop in schedule 40 pipe from the table or diagram above (psig per 100 ft pipe)
d40 = inside diameter schedule 40 pipe (inches)
d = actual inside diameter (inches)
Air, LNG, LPG and other common gas properties, pipeline capacities, sizing of relief valves.
Yearly power cost for operating an air compressor.
Pipe line sizing compressed air
Friction loss in air hoses vs. operating pressure.
Compressed air supply to laboratories.
Calculate pressure drop in compressed air pipe lines with a nomograph diagram.
Pressure loss in compressed air pipe lines.
Air pipe lines capacities at pressure 100 psi (6.9 bar).
Capacities of compressed air pipelines - pressure ranging 5 - 250 psi (0.5 - 17 bar).
Pressure drop in compressed air pipe lines.
Calculating air receivers capacity.
Calculate horsepower required by air compressors.
Pressure loss in pneumatic tubes - sizes ranging 5 - 36 mm.