Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

# Air Ducts - Major Friction Loss vs. Temperature and Pressure

## The influence of temperature and air pressure on major friction loss.

Air ducts friction loss and pressure drop diagrams are normally made for air at Normal Temperature and Pressure (NTP) condition - with a temperature of 20 oC and a atmospheric pressure of 1 bar.

### Influence of Temperature

The friction coefficient in the D'Arcy-Weisbach Equation increases with higher temperature but the coefficient will also be outweighed by the reduced pressure loss due to reduced density of the air.

• the pressure loss in an air duct is reduced with higher temperature

With air temperature other than 20 oC - a "Temperature Compensating Coefficient" can be used to modify the pressure loss:

Δp = kt ΔpNTP         (1)

where

Δp = actual friction loss (pressure or head)

kt = Temperature Compensating Coefficient

ΔpNTP = friction loss at NTP conditions (pressure or head)

"Temperature Compensating Coefficient" for various air temperatures:

### Example - Air with Temperature 100oC

For air with temperature 100oC the "Temperature Compensating Coefficient" is approximately 0.83. So,

• the pressure loss in air with temperature 100oC is approximately 83 % of the pressure loss in air at standard NTP conditions 20 oC

### Influence of Pressure

If the actual pressure differ from atmospheric pressure (1 bar abs) - friction loss in air ducts should be compensated with a "Pressure Compensating Coefficient":

Δp = kp ΔpNTP         (2)

where

Δp = actual friction loss (pressure or head)

kp = Pressure Compensating Coefficient

ΔpNTP = friction loss at NTP conditions (pressure or head)

The "Pressure Compensating Coefficient" can be estimated for various pressures from the diagram below:

• 1000 mbar = 1 bar = 105 Pa (N/m2) = 0.1 N/mm2 = 10,197 kp/m2 = 10.20 m H2O = 0.9869 atm = 14.50 psi (lbf/in2) = 106 dyn/cm2 = 750 mmHg

## Related Topics

• Ventilation - Systems for ventilation and air handling - air change rates, ducts and pressure drops, charts and diagrams and more.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

## Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.

Temperature

oC
oF

Length

m
km
in
ft
yards
miles
naut miles

Area

m2
km2
in2
ft2
miles2
acres

Volume

m3
liters
in3
ft3
us gal

Weight

kgf
N
lbf

Velocity

m/s
km/h
ft/min
ft/s
mph
knots

Pressure

Pa (N/m2)
bar
mm H2O
kg/cm2
psi
inches H2O

Flow

m3/s
m3/h
US gpm
cfm

8 17