An acoustic noise calculation of a ventilation system can follow the procedure indicated in the example below:
Sound and Noise Sources
Estimate all sound power sources.
1. Estimate the Sound Power Level from the Fan - LN
Enter the manufacturer's sound power data or calculate the fan sound power.
2. Add Safety factors
Add safety factors - 3 dB is recommended.
Estimate the attenuation in the system.
10. Room and terminal effect
The sound pressure levels - Lp - are converted to sound power level - Lw - at the terminals. The acoustic characteristics of the room as well as the number and location of the terminals must be considered.
a) Determine the acoustic characteristics of the room. In this example an average sound absorption for the room is used.
b) Determine whether the receiver are in the direct or reverberant field. In the example the listener is approximately 1.5 m from the terminal.
c) Find the rooms absorption characteristics. In the example the absorption for the walls, ceiling, floor, persons, curtains and their areas, is calculated to 30 m2 Sabine. According a) and c) the attenuation is 8 dB.
d) Determine how many terminals the listener are influenced by. Note! Remember to include supply and return fans. In the example the listener are influenced by two terminals. From c) we subtract 3 dB.
The attenuation from the terminal to the room is 5 dB. The values are entered in the example.
11. Allowance for end reflection
In the example the duct dimension is 250 mm. Attenuation due to end reflection is entered below.
12. Duct work attenuation
13. Elbow attenuation
Calculate the attenuation in the elbows.
14. Power-level split, branch to terminals
Determine the allowance for split - branch to terminals.
15. Power-level split, main duct to branch duct
Determine the allowance for split - main duct to branch.
16. Other attenuation
Add attenuation from other components.
Calculate Resulting Sound Power and Required additional Attenuation
20. Resulting Sound Power Fan
Subtract summarized attenuation from the fan sound power - inclusive safety factors
21. Sound pressure level criterion
22. Silencer requirements
The silencer must be selected to provide the necessary attenuation. Manufacturer's data are preferred.
Example - Acoustic Calculation of a Ventilation System
You can save and modify your own copy of the example if you are signed into your Google Account.
Room acoustics and acoustic properties, decibel A, B and C, Noise Rating (NR) curves, sound transmission, sound pressure, sound intensity and sound attenuation.
Heating, ventilation and air conditioning systems - design and dimensions.
Noise is usually defined as unwanted sound - noise, noise generation, silencers and attenuation in HVAC systems.
Ventilation systems can be classified by functions, distribution strategies or by ventilation principles.
Sound attenuation vs. frequency in rotating heat exchangers.
TheBlade Pass Frequency noise generated by a fan can be very intense and varies with the number of blades and the rotation velocity.
An online Noise Rating (NR) calculator.
The Noise Rating (NR) Curve used to determine acceptable indoor environments for hearing preservation, speech communication and annoyance.
The speed and attenuation of sound in moist air varies with sound frequency and air humidity.
Sound attenuation from main ducts to branch ducts.
Low frequency noise transferred from main duct to end terminals is reflected back to main duct.
Sound Pressure is the force of sound on a surface perpendicular to the propagation of sound.
Noise attenuation in unlined sheet-metal ducts.
Noise in a ventilation system can be reduced by reactive, diffuser type, active and/or dissipative silencers.