Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

Ventilation Systems - Acoustic Calculation Procedure

Acoustic noise calculation procedure HVAC systems.

An acoustic noise calculation of a ventilation system can follow the procedure indicated in the example below:

Sound and Noise Sources

Estimate all sound power sources.

1. Estimate the Sound Power Level from the Fan - LN

Enter the manufacturer's sound power data or calculate the fan sound power.

Add safety factors - 3 dB is recommended.

Attenuation

Estimate the attenuation in the system.

10. Room and terminal effect

The sound pressure levels - Lp - are converted to sound power level - Lw - at the terminals. The acoustic characteristics of the room as well as the number and location of the terminals must be considered.

a) Determine the acoustic characteristics of the room. In this example an average sound absorption for the room is used.

b) Determine whether the receiver are in the direct or reverberant field. In the example the listener is approximately 1.5 m from the terminal.

c) Find the rooms absorption characteristics. In the example the absorption for the walls, ceiling, floor, persons, curtains and their areas, is calculated to 30 m2 Sabine. According a) and c) the attenuation is 8 dB.

d) Determine how many terminals the listener are influenced by. Note! Remember to include supply and return fans. In the example the listener are influenced by two terminals. From c) we subtract 3 dB.

The attenuation from the terminal to the room is 5 dB. The values are entered in the example.

11. Allowance for end reflection

In the example the duct dimension is 250 mm. Attenuation due to end reflection is entered below.

12. Duct work attenuation

Calculate the attenuation in unlined and lined ducts. Note that the table and diagrams list the attenuation in dB/m.

13. Elbow attenuation

Calculate the attenuation in the elbows.

14. Power-level split, branch to terminals

Determine the allowance for split - branch to terminals.

15. Power-level split, main duct to branch duct

Determine the allowance for split - main duct to branch.

Calculate Resulting Sound Power and Required additional Attenuation

20. Resulting Sound Power Fan

Subtract summarized attenuation from the fan sound power - inclusive safety factors

21. Sound pressure level criterion

Determine the sound pressure level criteria. This table indicates acceptable levels at different locations. Check against domestic rules.

In the example below Noise Rating - NR30 - is used as a criterion. NR-values are entered in line 1.

22. Silencer requirements

The silencer must be selected to provide the necessary attenuation. Manufacturer's data are preferred.

Example - Acoustic Calculation of a Ventilation System

You can save and modify your own copy of the example if you are signed into your Google Account.

Related Topics

• Acoustics - Room acoustics and acoustic properties, decibel A, B and C, Noise Rating (NR) curves, sound transmission, sound pressure, sound intensity and sound attenuation.
• Noise and Attenuation - Noise is usually defined as unwanted sound - noise, noise generation, silencers and attenuation in HVAC systems.
• HVAC Systems - Heating, ventilation and air conditioning systems - design and dimensions.

Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.

Temperature

oC
oF

Length

m
km
in
ft
yards
miles
naut miles

Area

m2
km2
in2
ft2
miles2
acres

Volume

m3
liters
in3
ft3
us gal

Weight

kgf
N
lbf

Velocity

m/s
km/h
ft/min
ft/s
mph
knots

Pressure

Pa (N/m2)
bar
mm H2O
kg/cm2
psi
inches H2O

Flow

m3/s
m3/h
US gpm
cfm

3 10