Performance and efficiency rating of heat pumps.
Several methods can be used to rate heat pump performance and efficiency:
COP - Coefficient of Performance
The Coefficient of Performance - COP - is the ratio of heat output to the amount of energy input for a heat pump.
COP can be expressed as
COP = hh / hw (1)
COP = Coefficient of Performance
hh = heat produced (Btu/h, J, kWh)
hw = equivalent electric energy input (Btu/h, J, kWh) = 3413 Pw
Pw = electrical input energy (W)
If a heat pump delivers 3 units of heat for every unit of energy input - the COP is 3.
- 1 kW = 1000 W = 3413 Btu/h
Example - COP Heat Pump
A heat pump deliver 60000 Btu/h with a total electric input of 9 kW:
COP = (60000 Btu/h) / (3413 (9 kW))
A heat pump deliver 50000 Btu/h with a total input of 7 kW:
COP = (50000 Btu/h) / (3413 (7 kW))
Maximum theoretical efficiency for a heating process is
COPheating = Th / (Th - Tc) (1b)
COPheating = Coefficient of Performance - heating process
Th = absolute temperature on the hot side (K)
Tc = absolute temperature on the cold side (K)
Maximum theoretical efficiency for a cooling process is
COPcooling = Tc / (Th - Tc) (1c)
COPcooling = Coefficient of Performance - cooling process
Note! - the efficiency of a cooling or heating process can be increased by reducing the temperature difference (Th - Tc) between the hot and cold side.
A heating process with a lower hot temperature - like achievable in a piped floor system - will increases the efficiency compared to a system with higher hot temperature - like a heating panel system. The opposite for a cooling process - a lower cold temperature will increase the efficiency.
Example - Maximum Heat Pump Efficiency
An air to air heat pump operates between temperature -5 oC on the cold side and temperature 40 oC on the hot side. The maximum theoretical efficiency can be calculated by using (1b) as
COPheating = (40 + 273) / ((40 + 273) - (-5 + 273))
The typical practical value for a heat pump is in the range 2 - 4.
EER - Energy Efficiency Ratio
The Energy Efficiency Ratio - EER - is a measure of the cooling efficiency of a heat pump.
EER can be expressed as
EER = hc / Pw (2)
EER = Energy Efficiency Rating
hc = cooling heat (Btu/h)
Pw = electrical power (W)
Example - EER
An air conditioner or heat pump in cooling mode draws 1000 W of electric power to produce 10000 Btu/h of cooling. The EER can be calculated as
EER = (10000 Btu/h) / (1000 W)
HSPF - Heating Season Performance Factor
The Heating Season Performance Factor - HSPF - is a measure of the overall heating efficiency of a heat pump during the season.
HSPF = hs / 1000 Pws (3)
hs = heat produced during the season (Btu)
Pws = electrical power consumed during the season (kWh)
The HSPF can be regarded as an "average" COP for an entire heating season. It is common to compare BTUs of heat output to watts of electrical energy input. HSPF of 6.8 can be compared with an average COP of 2. A HSPF in the range of 5-7 is acceptable.
Example - Heat Pump Heating Season Performance Factor
For a heat pump deliver 120,000,000 Btu during the season when consuming 15,000 kWh the HSPF can be calculated as
HSPF = (120000000 Btu) / (1000 (15000 kWh))
SEER - Seasonal Energy Efficiency Ratio
Seasonal Energy Efficiency Ratio is a measure of the seasonal cooling efficiency of a heat pump or a consumer central air conditioning system.
The SEER should be at least 13 to be sold in the United States. SEER above 20 is a very efficient system.