Refrigeration Formulas
Calculate compression work, coefficients of performance and more.
Compression Work
Compressor work can expressed as
W = h q (1)
where
W = compression work (Btu min)
h = heat of compression (Btu/lb)
q = refrigerant circulated (lb/min)
Compression Horsepower
Compression horsepower can be expressed as
P = W / 42.4 (2)
where
P = compression power (hp)
W = compression work (Btu min)
Alternatively
P = c / (42.4 COP) (2b)
where
P = compression power (hp)
c = capacity (Btu/min)
COP = coefficient of performance
Compression horsepower per Ton
p = 4.715 / COP (2c)
where
p = compressor horsepower per Ton (hp/Ton)
COP = coefficient of performance
COP  Coefficient of Performance
COP = NRE / h (3)
where
COP = Coefficient of Performance
NRE = Net Refrigeration Effect (Btu/lb)
h = heat of compression (Btu/lb)
Net Refrigeration Effect
Net refrigeration effect can be expressed as
NRE = h _{ l }  h _{ e } (4)
where
NRE = Net Refrigeration Effect (Btu/lb)
h _{ l } = enthalpy of vapor leaving evaporator (Btu/lb)
h _{ e } = enthalpy of vapor entering evaporator (Btu/lb)
Capacity
c = q NRE (5)
where
c = capacity (Btu/min)
q = refrigerant circulated (lb/min)
NRE = Net Refrigeration Effect (Btu/lb)
Compressor Displacement
d = c v / NRE (6)
where
d = compressor displacement (ft ^{ 3 } /min)
c = capacity (Btu/min)
v = volume of gas entering compressor (ft ^{ 3 } /lb)
NRE = Net Refrigeration Effect (Btu/lb)
Heat of Compression
h = h _{ lc }  h _{ ec } (7)
where
h = heat of compression (Btu/lb)
h _{ lc } = enthalpy of vapor leaving compressor (Btu/lb)
h _{ ec } = enthalpy of vapor entering compressor (Btu/lb)
Volumetric Efficiency
μ = 100 w _{ a } / w _{ t } (8)
where
μ = volumetric efficiency
w _{ a } = actual weight of refrigerant
w _{ t } = theoretical weight of refrigerant
Compression Ratio
CR = p _{ h } / p _{ s } (9)
where
CR = compression rate
p _{ h } = head pressure absolute (psia)
p _{ s } = suction pressure, absolute (psia)
Related Topics

Air Conditioning
Air Conditioning systems  heating, cooling and dehumidification of indoor air for thermal comfort.
Related Documents

Calculating Cooling Loads
Calculating chiller and cooling tower refrigeration loads  in tons. 
Cooling Load  Convert between kW/ton to COP or EER
Convert between cooling load units like kW/ton, COP and EER. 
Cooling Power vs. Airflow and Duct Sizes
Typical relations between cooling power (tons cooling), air flow and duct size 
Net Refrigeration Effect
The quantity of heat absorbed from a refrigerated space. 
Refrigerants  Environmental Properties
Physical and environmental properties of some common refrigerants. 
Refrigeration Machinery  Required Ventilation
Ventilation required for refrigeration machinery and compressors in hot areas.