Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

# Boiler Water - Total Dissolved Solids (TDS)

When a boiler generates steam impurities in the feed water will concentrate in the boiler water. When the concentration of impurities becomes higher, foam is generated and the volume of the boiling water starts to increase. As a result - more and more low quality wet steam will be generated.

The concentration of impurities is often termed TDS - Total Dissolved Solids (ppm) and can be measured using a conductivity or density method.

### Measuring TDS with the density method

TDS = 1.1 106 (ρ - 1)                                   (1)

where

TDS = Total Dissolved Solids (ppm)

ρ = relative density of the boiler water at 15.5oC

This is a manual method requiring measuring a cooled down sample with a very sensitive hydrometer.

### Measuring TDS with the conductivity method

TDS = 0.7 σ                                      (2)

where

σ = conductivity (μs/cm)

This method can be used with an automatic resistance meter controlling the blow down cycles of the boiler. Note that electrolytic polarisation of the probe may be a problem and that an ac (amplitude current) resistance meter normally is used. Be also aware that the  conductivity increases with temperature.

### TDS Range

Boilers are normally operated in the range 2000 - 3500 TDS.

Boiler Water - Total Dissolved Solids (TDS)
TDS
(ppm)
Conductivity
(μs/cm)
Relative Density
0 0 1.00000
1000 2000 1.00091
2000 4000 1.00182
3000 6000 1.00273
4000 8000 1.00364

### Blow Down Rate

The boiler blow down rate depends on the

• steam consumption (steam used in the process and not returned as condensate to the boiler)
• concentration of impurities in the feed water
• maximum allowable TDS in the boiler

## Related Topics

### • Thermodynamics

Thermodynamics of steam and condensate systems.

## Related Documents

### Boiler Blowdown

Suspended solids in the feed water will remain in the boiler when steam is generated.

### Boiler Blowdown Rate

Calculate boiler blowdown rate.

### Boiler Feed Water - Chemistry and Impurity Limits

ABMA recommended feed water chemistry limits for steam boilers.

### Feed Water Treatment to Avoid Corrosion

Make-up water to steam boilers should be treated with oxygen scavengers to avoid serious corrosion problems.

### Soft or Hard Water

Carbonates dissolved in water.

### Solubility

The amount of a solute that can be dissolved in a solvent.

### Solubility of Air in Water

The amount of air that can be dissolved in water decreases with temperature and increases with pressure.

### Solubility of Gases in Water vs. Temperature

Solubility of Ammonia, Argon, Carbon Dioxide, Carbon Monoxide, Chlorine, Ethane, Ethylene, Helium, Hydrogen, Hydrogen Sulfide, Methane, Nitrogen, Oxygen and Sulfur Dioxide in water.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!