Temperatures and maximum distance between supports for pipes made of
- PVDF - PolyVinylidene Fluoride
- CPVC - Chlorinated Polyvinyl Chloride
- PVC - Polyvinyl Chloride
- PP - PolyPropylene
are indicated in the diagrams below.
- 1 ft (foot) = 0.3048 m
- T(oF) = [T(oC)](9/5) + 32
Dimensions of pipes and tubes, materials and capacities, pressure drop calculations and charts, insulation and heat loss diagrams.
Maximum distance between supports for ABS, PE, PVC, Fiberglass and Steel Pipes.
Standard dimensions and weight of PVC - Polyvinyl Chloride - and CPVC - Chlorinated Polyvinyl Chloride.
Dimensions of pressure rated PP pipes according ASTM F2389.
Maximum space between supports aand clips for copper tubes.
Maximum distance between CPVC pipe supports.
Maximum operating and bursting pressures of CPVC - Chlorinated Poly (Vinyl Chloride) - piping systems.
Support of Drain Waste and Vent - DWV - pipes.
Plastic piping systems for soil and waste discharge (low and high temperature) within the building structure.
Support spacing for reinforced Epoxy fiberglass pipes.
Recommended maximum support span between hangers - and rod sizes for straight horizontal pipes.
Friction head loss (ft/100 ft) vs. water flow in plastic pipes like PVC, PP, PE or PEH.
Maximum distance between PolyPropylene pipes supports.
Distance between PVC pipe supports.
Maximum operating and required burst pressure of PVC - Polyvinyl Chloride - pipe fittings.
Friction loss (psi/100 ft) and velocity for water flow in plastic PVC pipe schedule 40.
Maximum distance between PVDF pipe supports.
Recommended max. distance between steel pipe supports.