# Cooling and Heating Equations

## Latent and sensible cooling and heating equations - imperial units

### Sensible Heat

The sensible heat in a heating or cooling process of air (heating or cooling capacity) can be calculated in SI-units as

hs = cp ρ q dt                                              (1)

where

hs = sensible heat (kW)

cp = specific heat of air (1.006 kJ/kg oC)

ρ = density of air (1.202 kg/m3)

q = air volume flow (m3/s)

dt = temperature difference (oC)

Or in Imperial units as

hs = 1.08 q dt                                            (1b)

where

hs = sensible heat (Btu/hr)

q = air volume flow (cfm, cubic feet per minute)

dt = temperature difference (oF)

### Latent Heat

Latent heat due to the moisture in air can be calculated in SI-units as:

hl = q ρ hwe dwkg                                      (2)

where

hl = latent heat (kW)

ρ = density of air (1.202 kg/m3)

q = air volume flow (m3/s)

hwelatent heat of vaporization of water (2465.56 kJ/kg)

dwkg  = humidity ratio difference (kg water/kg dry air)

Or for Imperial units:

hl = 0.68 q dwgr                                      (2b)

or

hl = 4840 q dwlb                                     (2c)

where

hl= latent heat (Btu/hr)

q = air volume flow (cfm, cubic feet per minute)

dwgr = humidity ratio difference (grains water/lb dry air)

dwlb = humidity ratio difference (lb water/lb dry air)

### Total Heat - Latent and Sensible Heat

Total heat due to both temperature and moisture can be expressed in SI units as:

ht = q ρ dh                                            (3)

where

ht = total heat (kW)

q = air volume flow (m3/s)

ρ = density of air (1.202 kg/m3)

dh = enthalpy difference (kJ/kg)

Or - in imperial units:

ht = 4.5 q dh                                        (3b)

where

ht= total heat (Btu/hr)

q = air volume flow (cfm, cubic feet per minute)

dh = enthalpy difference (btu/lb dry air)

Total heat can also be expressed as:

ht = hs + hl

= 1.08 q dt + 0.68 q dwgr                                      (4)

### Example - Heating Air

An air flow of one cfm is heated from 32 to 52oF. Using (1) the sensible heat added to the air can be expressed as:

hs = 1.08 (1 cfm) ((52 oF) - (32 oF))

= 21.6 (Btu/hr)

#### Sensible Heat Load and Required Air Volume Chart

Sensible heat load and required air volume to keep the temperature constant at various temperature differences between make up air and room air:

#### Latent Heat Load and Required Air Volume Chart

Latent heat load - humidifying and dehumidifying - and required air volume to keep temperature constant at various temperature differences between entering air and room air are indicated in the chart below:

### SHR - Sensible Heat Ratio

The Sensible Heat Ratio can be expressed as

SHR = hs / ht                              (6)

where

SHR = Sensible Heat Ratio

hs = sensible heat

ht = total heat (sensible and latent)

## Related Topics

• Air Conditioning - Air Conditioning systems - heating, cooling and dehumidification of indoor air for thermal comfort

## Search the Engineering ToolBox

- "Search is the most efficient way to navigate the Engineering ToolBox!"

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your SketchUp model with the Engineering ToolBox - SketchUp Extension/Plugin - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

Translate the Engineering ToolBox!