# Sensible Heat Ratio - SHR

## Sensible Heat Ratio - SHR - is defined as the sensible heat or cooling load divided by the total heat or cooling load

The Sensible Heat Ratio - SHR - express the ratio between the sensible heat load and the total heat load and can be expressed as:

SHR = qs / qt

=  qs / (qsql)                                                (1)

where

SHR = sensible heat ratio (ratio of sensible heat load to total heat load)

qs = sensible heat load (kW, Btu/hr)

qt = total heat load - sensible heat and latent heat (kW, Btu/hr)

ql = latent heat load (kW, Btu/hr)

For an air flow (1) can be modified to:

SHR = cp (to - ti) / (ho - hi)                                              (2)

where

cp = specific heat air (1.005 kJ/kgoC, 0.240 Btu/lboF)

to = outlet air temperature (oC, oF)

ti = inlet air temperature (oC, oF)

ho = outlet moist air enthalpy (kJ/kg, Btu/lb)

hi = inlet moist air enthalpy (kJ/kg, Btu/lb)

### Example - SHR

The inlet temperature to a room with some people is 20 oC. The relative moisture of the inlet air is 50%. From the Mollier chart the enthalpy of the inlet air is 37 kJ/kg.

The outlet temperature is 26 oC and the relative moisture of the outlet air is 40%. From the Mollier chart the enthalpy of the outlet air is 47 kJ/kg.

The Sensible Heat Ratio can be calculated as

SHR = (1.005 kJ/kgoC) ((26 oC) - (20 oC)) / ((47 kJ/kg) - (37 kJ/kg))

= 0.6

### General Design Values

• Auditoriums, Theaters - SHR : 0.65 - 0.75
• Apartments - SHR : 0.80 - 0.95
• Banks, Court Houses, Municipal Buildings - SHR : 0.75 - 0.90
• Churches - SHR : 0.65 - 0.75
• Dining Halls - SHR : 0.65 - 0.80
• Computer Rooms - SHR : 0.80 - 0.95
• Cocktail Lounges, Bars, Taverns, Clubhouses, Nightclubs - SHR : 0.65 - 0.80
• Jails - SHR : 0.80 - 0.95
• Hospital Patient Rooms, Nursing Home, Patient Rooms - SHR : 0.75 - 0.85
• Kitchens - SHR : 0.60 - 0.70
• Libraries, Museums - SHR : 0.80 - 0.90
• Malls, Shopping Centers - SHR : 0.65 - 0.85
• Medical/Dental Centers, Clinics and Offices - SHR : 0.75 - 0.85
• Motel and Hotel Public Areas - SHR : 0.75 - 0.90
• Motel and Hotel Guest Rooms - SHR : 0.80 - 0.95
• Police Stations, Fire Stations, Post Offices - SHR : 0.75 - 0.90
• Precision Manufacturing - SHR : 0.80 - 0.95
• Restaurants - SHR : 0.65 - 0.80
• Residences - SHR : 0.80 - 0.95
• Retail, Department Stores - SHR : 0.65 - 0.90
• Other Shops - SHR : 0.65 - 0.90
• School Classrooms - SHR : 0.65 - 0.80
• Supermarkets - SHR : 0.65 - 0.85

## Related Topics

• Air Conditioning - Air Conditioning systems - heating, cooling and dehumidification of indoor air for thermal comfort
• Air Psychrometrics - The study of moist and humid air - psychrometric charts, Mollier diagrams, air-condition temperatures and absolute and relative humidity and moisture content

## Tag Search

• en: sensible heat ratio shr factor shf
• es: relación de calor sensible factor de shr SHF
• de: fühlbare Wärme-Verhältnis shr Faktor SHF

## Search the Engineering ToolBox

- "the most efficient way to navigate!"

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your SketchUp model with the Engineering ToolBox - SketchUp Extension/Plugin - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

Translate the Engineering ToolBox!