- Resources, Tools and Basic Information for Engineering and Design of Technical Applications!
The stack or flue effect occurs when the outdoor temperature is lower than indoor temperature.
The stack or flue effect occurs when the outdoor temperature is lower than the indoor temperature. The
warm indoor air is lighter than cooler outside air.
The air flow can be estimated as
Q = 9.4 A (h (t r - t o)) 1/2 (1)
Q = rate of air flow (ft 3/min)
A = free area of inlets and outlets - assumed equal (ft 2)
h = height from inlets to outlets (ft)
t r = average room temperature at height h ( oF)
t o = outdoor temperature ( oF) Flow of Air in Natural-Draft Flues
Systems for ventilation and air handling - air change rates, ducts and pressure drops, charts and diagrams and more.
Online calculator, figures and tables showing density, specific weight and thermal expansion coefficients of air at temperatures ranging -100 to 1600 °C (-140 to 2900 °F) at atmospheric and higher pressure - Imperial and SI Units.
Air flow - volume and velocity - due to stack or flue effect caused by indoor hot and outdoor cold temperature difference.
Search is the most efficient way to navigate the Engineering ToolBox.
About the Engineering ToolBox!
We don't collect information from our users. More about
This page can be cited as
The Engineering ToolBox (2008).
Stack or Flue Effect. [online] Available at: https://www.engineeringtoolbox.com/stack-flue-effect-d_1424.html [Accessed Day Month Year].
Modify the access date according your visit.