Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

# Electric Circuits Voltage Drop

## Ohm's law and voltage drop in electric circuits.

Voltage drop in an electric circuit can be calculated using Ohm's law as

U = R I                (1)

where

U = voltage drop (volts, V)

R = electrical resistance in the electric circuit (ohms, Ω)

I = current (amps, A)

### Example - Voltage Drop

Voltage drop in a 100 ft power line:

The electric resistance in the circuit can be calculated

R = (1.02 Ω/1000 ft) (100 ft) 2

= 0.204 Ω

The voltage drop in the circuit can be calculated with (1)

U = (0.204 Ω) (10 amps)

= 2.04 volts

### Circular mils and Voltage drop

Voltage drop can also be calculated using mils like

U = K P L I / A                       (2)

where

K = specific resistivity (Ω - circular mils/foot)

P = phase constant = 2 (for single phase) = 1.732 (for three phase)

L =  wire length (ft)

A = wire area (circular mils)

Specific electric resistivity for different types of wire materials

• Solid Copper, K = 11 (temp 77oF - 121oF), K = 12 (temp 122oF - 167oF)
• Solid Aluminum, K = 18 (temp 77oF - 121oF), K = 20 (temp 122oF - 167oF)
• Stranded Copper, K = 11 (temp 77oF - 121oF), K = 12 (temp 122oF - 167oF)
• Stranded Aluminum, K = 19 (temp 77oF - 121oF), K = 20 (temp 122oF - 167oF)

### Example - Specific resistivity and Voltage Drop

With values from the example above the voltage drop can be calculated as

U = (11 ohm - circular mils/foot) 2 (100 ft) (10 A) / (10400 mils)

= 2.11 V

### Copper Conductor - Voltage Drop Table

The voltage drop in a copper conductor can be estimated with

U = f I L                          (3)

where

f = factor from table below

I = current (amps)

L = conductor length (ft)

SizeFactor
- f -
AWGMetric
mm2
Single-phase3-phase
14 2.08 0.476 0.42
12 3.31 0.313 0.26
10 5.26 0.196 0.17
8 8.37 0.125 0.11
6 13.3 0.0833 0.071
4 21.2 0.0538 0.046
3 0.0431 0.038
2 33.6 0.0323 0.028
1 42.4 0.0323 0.028
1/0 53.5 0.0269 0.023
2/0 67.4 0.0222 0.020
3/0 85.0 0.019 0.016
4/0 107.2 0.0161 0.014
250 0.0147 0.013
300 0.0131 0.011
350 0.0121 0.011
400 0.0115 0.009
500 0.0101 0.009

## Related Topics

### • Electrical

Electrical units, amps and electrical wiring, wire gauge and AWG, electrical formulas and motors.

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the SketchUp Pro Sketchup Extension Warehouse!

Translate

## Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.

## Citation

• The Engineering ToolBox (2009). Electric Circuits Voltage Drop. [online] Available at: https://www.engineeringtoolbox.com/voltage-drop-d_1550.html [Accessed Day Month Year].

Modify access date.

. .

close

6 6