Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

# Ventilation Efficiency

## The efficiency of a ventilation system may be related to temperature and/or pollution concentrations

The efficiency of ventilation systems are in general related to

• temperatures, and/or
• pollution and contaminants concentrations

in supply air, room air and outlet air.

### Temperature Efficiency

Temperature efficiency of a ventilation system can be calculated as

μt = (to - ts) / (trz - ts)                                    (1)

where

μt = temperature efficiency

to = outlet air temperature (oC, oF)

ts = supply air temperature (oC, oF)

trz = room temperature in the residence zone - mean value (oC, oF)

The potential efficiency of a system depends on the ventilation principle used.

#### Short Cut Ventilation

With "short cuts" the outlet temperature is close to the supply temperature and the ventilation efficiency approaches to  zero.

#### Mixed Ventilation

With mixed ventilation the outlet temperature is close to the room temperature in the residential zone and the ventilation efficiency approaches to one.

#### Displacement Ventilation

With displacement ventilation the outlet temperature is higher than the temperature in the residence zone and in the supply air. The ventilation efficiency is higher (often much higher depending on the actual conditions) than one.

#### Piston Ventilation

Piston ventilation is an extreme variant of displacement ventilation. The efficiency is always higher than one.

### Pollution Efficiency

Pollution or contaminant efficiency may calculated as

μv = co / crz                                         (2)

where

μv = ventilation efficiency

co = pollution concentration in the outlet air (kg/m3, lbm/ft3)

crz pollution concentration in the air in the residence zone, mean value (kg/m3, lbm/ft3)

The pollution or contaminant concentration in the outlet air can be expressed as

co = qs / qv                                         (3)

where

qs = pollution flow in the air (kg/s)

qv = outlet air flow (m3/s)

The mean pollution concentration in the room can be expressed as

crz = G / V                                         (4)

where

crz = pollution concentration in the room (kg/m3)

G = total pollution in the room (kg)

V = volume of the room (m3)

#### Short Cut Ventilation

With "short cuts" the pollution concentration in the outlet is less than in the air in the residential zone and the ventilation efficiency will approach to zero.

#### Mixed Ventilation

With mixed ventilation the outlet pollution concentration is close to the pollution concentration in the residential zone and the ventilation efficiency will approach to one.

#### Displacement Ventilation

With displacement ventilation the outlet pollution concentration is higher than the pollution concentration in the residence zone. The ventilation efficiency is higher (often much higher depending on the actual conditions) than one.

#### Piston Ventilation

Piston ventilation is an extreme variant of the displacement ventilation . The efficiency is always higher than one.

## Related Topics

• Ventilation - Systems for ventilation and air handling - air change rates, ducts and pressure drops, charts and diagrams and more

## Tag Search

• en: ventilation efficiency temperature polution contaminants

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro .Add the Engineering ToolBox extension to your SketchUp from the SketchUp Pro Sketchup Extension Warehouse!

## Privacy

We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.

Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.

## Citation

• Engineering ToolBox, (2008). Ventilation Efficiency. [online] Available at: https://www.engineeringtoolbox.com/ventilation-efficiency-d_1040.html [Accessed Day Mo. Year].

Modify access date.

. .

close

11 29