Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!
- search is the most efficient way to navigate the Engineering ToolBox!
Ventilation systems - air intakes and outlets - rules of thumbs
- Intakes should be at least 0.15 m (0.5 ft) above the terrain. In areas with traffic the intake should be at least 5 m (16 ft) above the terrain
- The distance between intake, firewalls and surrounding buildings must be according the rules of the local authorities
- Short cutting intake air with used outlet air must be avoided
- An air intake should be located in a position where the wind influence on the pressure conditions within the system is limited
- Air velocities in the intake openings should not exceed 2.5 m/s (~ 500 ft/min)
- Outlets should go direct out in unrestricted area
- Short cuts with intake air, window openings and residence areas must be avoided
- The distance between outlet, firewalls and surrounding buildings must be according the rules of the local authorities
- An air outlet should be located in a position where the wind influence on the pressure conditions within the system is limited
- The air velocity through the outlet should not exceed 3 - 15 m/s (~ 500 - 3000 ft/min)
Translate this page to
About the Engineering ToolBox!
We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.
Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.
This page can be cited as
- Engineering ToolBox, (2003). Air Intakes and Outlets. [online] Available at: https://www.engineeringtoolbox.com/air-intake-outlet-d_137.html [Accessed Day Mo. Year].
Modify access date.
Scientific Online Calculator
4 15 .