# Pumps - Specific Suction Speed

## Specific Suction Speed can be used to determine what general pump design to use for maximum efficiency

Specific Suction Speed can be used to determine what pump geometry - radial, mixed flow or axial - to use for maximum efficiency and to prevent cavitation. Suction Specific Speed is commonly used to estimate pumps safe operating ranges.

Suction Specific Speed is dimensionless and can be expressed as

Nss = ω q1/2 / NPSHr3/4                                (1)

where

Nss = Suction Specific Speed

ω = pump shaft rotational speed (rpm)

q = flow rate capacity (m3/h, l/s, m3/min, US gpm, British gpm) at the Best Efficiency Point (BEP)

Specific Suction Speed can be compared with Specific Speed but instead of using the total head of the pump, the Required Net Positive Suction Head (NPSHr) is used.

As a rule of thumb the Specific Suction Speed should be below 8500 (calculated with US gpm) to avoid cavitation.

### Online Specific Suction Speed Pump Calculator

The calculator below can used to calculate pump specific suction speed:

ω - pump shaft rotational speed (rpm)

q -  flow rate (m3/h, l/s, m3/min, US gpm, British gpm)

NPSHr - Required Net Positive Suction Head (m, ft)

Note! When comparing pumps and their documentation - be aware of the units used.

Suction Specific Speed - Ss - is useful in determining the required operating conditions on the suction side of a pump. Ss have the same value for geometrically similar pumps.

Empirical studies indicates that safe operating ranges from Best Efficiency Points (BEP) are more narrow at higher Suction Specific Speeds. Pump designs with Ssd (US units) less than 11000 operates more stable and are more reliable.

### Convert between Imperial units (gpm) and Metric units (m3/h, l/s)

• Nss (US gpm) = 1.63 Nss (metric l/s) = 0.86 Nss (metric m3/h)
• Nss (Metric l/s) = 0.614 Nss (US gpm)
• Nss (Metric l/s) = 0.67 Nss (British gpm)

### Example - Specific Suction Speed

The available Net Suction Head - NPSHa - of a pump is determined to be 20 ft. With rotational speed 1750 rpm and flow rate 500 US gpm the Specific Suction Speed can be calculated as

Nss = (1750 rpm) (500 gpm)1/2 / (20 ft)3/4

= 4138

Well below the limit 8500 to avoid cavitation.

### Double Suction Type Pumps

For a double suction pump the flow at the inlet is divided by two. Using a double suction pump is one way of meeting system NPSH and obtaining a higher head.

## Related Topics

• Pumps - Piping systems and pumps - centrifugal pumps, displacement pumps - cavitation, viscosity, head and pressure, power consumption and more

## Tag Search

• en: suction specific speed pumps
• es: bombas de velocidad específica de succión
• de: Saugzahl Pumpen

## Search the Engineering ToolBox

- "the most efficient way to navigate!"

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your SketchUp model with the Engineering ToolBox - SketchUp Extension/Plugin - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

Translate the Engineering ToolBox!