Overall pump and fan efficiency is the ratio - power actually gained by the fluid - to shaft power supplied
For a fluid flow process involving a pump or fan the overall efficiency is related to the
loss in the pump or fan.
Hydraulic Loss and Hydraulic Efficiency
Hydraulic loss relates to the construction of the pump or fan, and is caused by the friction between the fluid and the walls, acceleration and retardation of the fluid and the change of the fluid flow direction.
The hydraulic efficiency can be expressed as:
ηh = w / (w + wl) (1)
ηh = hydraulic efficiency
wl = specific work lost due to hydraulic effects
Mechanical Loss and Mechanical Efficiency
Mechanical components - as transmission gear and bearings - generates a mechanical loss that reduces the power transferred from the motor shaft to the pump or fan impeller.
The mechanical efficiency can be expressed as:
ηm = (P - Pl) / P (2)
ηm = mechanical efficiency
P = power transferred from the motor to the shaft
Pl = power lost in the transmission
Volumetric Loss and Volumetric Efficiency
Due to leakage of fluid between the back surface of the impeller hub plate and the casing, or through other pump components - there is a volumetric loss reducing the pump efficiency.
The volumetric efficiency can be expressed as:
ηv = q / (q + ql) (3)
ηv = volumetric efficiency
q = volume flow out of the pump or fan
ql = leakage volume flow
Total Loss and Overall Efficiency
The overall efficiency is the ratio of power actually gained by the fluid to the shaft power supplied. The overall efficiency can be expressed as:
η = ηh ηm ηv (4)
η = overall efficiency
The losses in the pump or fan converts to heat transferred to the fluid and the surroundings. As a rule of thumb the temperature increase in a fan transporting air is approximately 1 oC.
Example - Hydraulic Efficiency for a Pump
An inline water pump works between pressure 1 bar (1 105 N/m2) and 10 bar (10 105 N/m2). Density of water is 1000 kg/m3. The hydraulic efficiency ηh = 0.91.
The actual water head (water column) can be calculated as:
h = (p2 - p1) / γ
= (p2 - p1) / ρ g
= ((10 105 N/m2) - (1 105 N/m2)) / (1,000 kg/m3) (9.81 m/s2)
= 91.7 m - water column
The pump must be constructed for the specific work:
wc = g h / ηh
= (9.81 m/s2) (91.7 m) / 0.91
= 988.6 m2/s2
The construction or design head is:
h = wc / g
= (988.6 m2/s2) / (9.81 m/s2)
= 100.8 m - water column
- en: pump fan efficiency