# Fan Affinity Laws

## Affinity laws can be used to calculate volume capacity, head or power consumption - when speed or rpm, and wheel diameters are changed

Sponsored Links

**The Affinity Laws** of centrifugal pumps or fans can be used to express the influence on volume capacity, head (pressure) or power consumption of a pump or fan due to

- change in
speedof wheel - revolutions per minute (rpm)- geometrically similarity - change in
impeller diameter

Note that the affinity laws for pumps are not identical with fans.

### Fan Affinity Laws

#### Volume Capacity

*The volume capacity of a centrifugal fan can be expressed like*

q_{1}/ q_{2}= (n_{1}/ n_{2})(d_{1}/ d_{2})^{3}(1)

where

q= volume flow capacity (m^{3}/s, gpm, cfm, ..)

n= wheel velocity - revolution per minute - (rpm)

d = wheel diameter

#### Head or Pressure

The head or pressure of a centrifugal fan can be expressed like

dp_{1}/ dp_{2}= (n_{1}/ n_{2})^{2}(d_{1}/ d_{2})^{2}(2)

where

dp= head or pressure (m, ft, Pa, psi, ..)

#### Power

The power consumption of a centrifugal fan can be expressed as

P_{1}/ P_{2}= (n_{1}/ n_{2})^{3}(d_{1}/ d_{2})^{5}(3)

where

P= power (W, bhp, ..)

**Changing the Wheel Velocity**

If the **wheel diameter is constant** - change in fan wheel velocity can simplify the affinity laws to

##### Volume Capacity

q_{1}/ q_{2}= (n_{1}/ n_{2}) (1a)

##### Head or Pressure

dp_{1}/ dp_{2}= (n_{1}/ n_{2})^{2}^{ }(2a)

##### Power

P_{1}/ P_{2}= (n_{1}/ n_{2})^{3}^{ }(3a)

**Note!** If the speed of a fan is increased with *10%*

- the volume flow increases with
*10%* - the head increases with
*21%* - the power increases with
*33 %*

If the volume flow capacity of an existing system is increased with *10%* the power supply is increased with 33%. The electrical motor and power supply may need an upgrade.

#### Fan Affinity Laws Calculator - Changing Wheel Velocity

Replace the default values with the actual values. The calculator is generic and can be used with all common units as long as the use is consistent.

**Changing the Impeller Diameter**

If wheel velocity is constant **a change in impeller diameter** can simplify the affinity laws to

##### Volume Capacity

q_{1}/ q_{2}=(d_{1}/ d_{2})^{3}(1b)

##### Head or Pressure

dp_{1}/ dp_{2}=(d_{1}/ d_{2})^{2}(2b)

##### Power

P_{1}/ P_{2}=(d_{1}/ d_{2})^{5}(3b)

#### Fan Affinity Laws Calculator - Changing Wheel Diameter

Replace the default values with the actual values. The calculator is generic and can be used with all common units as long as the use is consistent.

Sponsored Links