Heating Systems  Steam and Condensate Loads
Calculating steam and condensate loads in steam heated systems.
The two basic situations common when calculating steam and condensate loads in steam heated systems are
 heat transfer through areas
 heating up materials
Heat Transfer through Areas
Heat transfer through areas can be expressed as:
Q = U A dt (1)
where
Q = quantity of heat transferred trough the area
A = heat transfer area
dt = temperature difference between the steam and the secondary heated fluid
Heating up Materials
The heat needed to heat up materials can be expressed as:
Q = w c_{p} (t_{2}  t_{1}) (2)
where
w = weight of material
c_{p} = specific heat of the heated material (Check Material Properties to find specific heat for materials)
t_{1} = initial temperature of the heated material
t_{2} = final temperature of the heated material
Heat Rate
The heat rate is the heat transferred per unit of time.
Heat Transfer Rate through Areas
The formula for calculating the heat transfer rate for heat transfer through an area can be expressed as:
Q' = Q / (L h) = U A dt /(L h) (3)
where
L = Latent heat of evaporated (condensation) steam (Check Steam Tables to find latent heat, SI or Imperial Units)
h = available time
Heat Transfer Rate when heating up Materials
The formula for calculating the heat transfer rate for heating up materials can be expressed as:
Q' = Q / (L h) = w c_{p} (t_{2}  t_{1}) /(L h) (3b)
Related Topics

Steam and Condensate
Steam & condensate systems properties, capacities, pipe sizing, systems configuration and more.
Related Documents

Air Heating Systems
Air heating buildings  heat supply vs. air flow and temperature. 
Condensate Pipe Lines  Sizing
Flow and pressure loss in condensate return lines  SI Units. 
Condensation of Steam  Heat Transfer
Heat transfer when steam condensates. 
Heat Emission from Radiators and Heating Panels
The heat emission from a radiator or a heating panel depends on the temperature difference between the radiator and the surrounding air. 
Heat Loss from Buildings
Overall heat transfer loss from buildings  transmission, ventilation and infiltration. 
Heating Up Applications  Energy Required and Heat Transfer Rates
Energy required to heat up a substance. 
Insulated Steam Pipes  Condensate Generated
Heat loss from steam pipes generates condensate which must be drained from the system  imperial units. 
Sizing Steam Pipes (lb/h)
Steam is a compressible gas where the capacity of a pipe line depends on the size of the pipe and the steam pressure. 
Steam  Flow vs. kW Rating
Calculate steam flow rate vs. kW rating. 
Steam Heating Air
Calculate steam heated air systems. 
Steam Heating Processes  Load Calculating
Calculating the amount of steam in nonflow batch and continuous flow heating processes. 
Steam Heating Systems  Classifications
Steam systems carries heat through pipes from the boiler to consumers as heat exchangers, process equipment etc. 
Transmission Heat Loss through Building Elements
Heat loss through common building elements due to transmission, Rvalues and Uvalues  imperial and SI units.