# Sizing Swimming Pool Heaters

## Calculating outdoor swimming pool heaters

Sponsored Links

The necessary heat to increase and maintain the temperature of an outdoor pool can be expressed as

*h _{total} = h_{surface} + h_{heat-up} (1)*

*where*

*h _{total} = total heat load (btu/hr)*

*h _{surface} = heat loss through surface - mainly evaporation of water from the surface (btu/hr)*

*h _{heat-up} = heat load necessary to move the pool from the initial temperature (btu/hr)*

### Heat-Up Load

The heat-up load depends on the volume of the pool which can be expressed as

*V = l w d 7.5 (gal/ft ^{3}) (2)*

*where*

*V = volume (Gal)*

*l = length (ft)*

*w = width (ft)*

*d = depth (ft)*

The heat-up load can then be expressed as

*h _{heat-up} = V 8.34 (lbs/gal) dT_{w} 1.0 (Btu/lb ^{o}F) / dt (3)*

*where*

*dT _{w} = difference between initial temperature and the final temperature of the water (^{o}F)*

*dt = heat pick-up time (hr)*

### Swimming Pool Heat-Up Load or Heat-Up Time Calculator

Calculate heat-up load or heat-up time. Tip! Make a link to the mobile edition of this calculator on your smart phone home screen.

Add the required data for your swimming pool below. Note that you must use either "Heat-Up Load" or "Heat Pick-up Time" in the calculator.

Length (ft) | |

Width (ft) | |

Depth (ft) | |

Initial Temperature (^{o}F) | |

Final Temperature (^{o}F) | |

Heat-up Load (Btu/hr) | |

Heat Pick-up Time (hr) | |

Volume (gal) | |

Heat-up Load (Btu/hr) | |

Heat Pick-up Time (hr) |

### Surface Heat Loss due to Temperature Difference

The heat load necessary to cover up the surface loss due to temperature difference between pool surface and ambient air can be expressed as

*h _{surface} = k_{s} dT_{aw} A (4)*

*where*

*k _{s} = surface heat loss factor - for sheltered positions with average wind velocity 2 to 5 (mph), the surface heat loss factor is in the range 4 to 7 (Btu/hr ft^{2} ^{o}F)*

*dT _{aw} = temperature difference between the air and surface water in the pool (^{o}F)*

*A = surface area of the pool (ft ^{2})*

*Note that a major part of the heat loss from the swimming pool surface is due to evaporation of water from the surface. *

*Example - Pool Heating*

*A pool with dimensions length** 30 ft**, width **20 ft** and dept **6 ft** is heated from * *50 ^{o}F*

*to*

*75*

^{o}F*. The volume in the pool (in gallons) can be calculated as*

*V = (30 ft) (20 ft) (6 ft) (7.5 gal/ft ^{3}) *

* = 27000 (gal) *

*The heat-up heat required to heat the pool up in 24 hours can be calculated as *

* **h _{heat-up} = (27000 gal) (8.34 lbs/gal) ((75 ^{o}F) - (50^{ o}F)) (1.0 Btu/lb ^{o}F) / (24 hr)*

* = 234562 Btu/hr*

*1 Btu/hr = 2.931x10*^{-4}kW = 0.252 kcal/hr

*Note that this value is without the increased heat loss through the surface due to increased temeperature difference and increased evaporation when the temperature increase. *

*If the ambient temperature is **65 ^{ o}F*

*and the wind conditions is modereate, the heat loss through the surface due to temperature difference (when the pool is heated up) can be calculated as*

*h _{surface} = (5 Btu/hr ft^{2} ^{o}F) ((75 ^{ o}F) - (65 ^{o}F)) (30 ft) (20 ft)*

* = 30000 (Btu/hr)*

*Heat-up Load in SI-units*

*The heat-up load in SI-units can be calculated as *

*h _{heat-up} = ρ c_{p} l w d dT / dt (5)*

*where *

*h _{heat-up} = heat flow rate required (kW, kJ/s)*

*ρ = 1000 - density of water (kg/m ^{3})*

*c _{p} = 4.2 - specific heat capacity of water (kJ/kg^{o}C)*

*l = length of swimming pool (m) *

*w = width of swimming pool (m)*

*d = dept of swimming pool (m)*

*dT = difference between initial and final temperature ( ^{o}C)*

*dt = heat up time (sec) *

*Example - Heat-up Load in SI-units*

*The heat-up load for a swiming pool **12 m x 6 m x 1.5 m**, heated from **10*^{o}C* to **20 ^{o}C*

*in*

*10 hours*, can be calculated as

*h _{heat-up} = 1000 (kg/m^{3}) 4.2 (kJ/kg^{o}C) 12 (m) 6 (m) 1.5 (m) (20 (^{o}C) - 10 (^{o}C)) / (10 (hours) 3600 (sec/hours))*

* = 126 (kW)*

Sponsored Links

Sponsored Links

## Related Topics

## Related Documents

## Tag Search

- en: swimming pool heating heat-up time