# Air Ducts Minor Loss Coefficient Diagrams

## Minor loss coefficient diagrams for air ductwork, bends, expansions, inlets and outlets  - SI units

Minor loss in air ducts based on a summarized minor loss coefficients and air flow velocity:

• 1 Pa = 1 N/m2 = 1.4504x10-4 lb/in2 = 1x10-5 bar = 4.03x10-3 in water = 0.336x10-3 ft water = 0.1024 mm water = 0.295x10-3 in mercury = 7.55x10-3 mm mercury = 0.1024 kg/m2 = 0.993x10-5 atm

Minor loss for some common duct-work components like bends, expansions, inlets and outlets can be estimated from the diagrams below.

### Minor Loss Coefficients - Bends

The minor loss coefficients in 90o bends can be estimated with the diagram below.

The minor loss in bends 0 - 180o can be estimated with the equation

ξ0-180 = ξ90 α / 90                                            (1)

where

ξ0-180 = minor loss coefficient for the bend with the actual angle

ξ90 = minor loss coefficient for the 90o bend according the diagram above

α = angle of the actual bend

The minor loss coefficient in a 90o bend like the one below is 1.0.

## Related Topics

• Ventilation - Systems for ventilation and air handling - air change rates, ducts and pressure drops, charts and diagrams and more

## Tag Search

• en: minor loss air ducts diagram pressure drop flow pa
• es: aire pérdida menor conductos de presión diagrama pa flujo gota
• de: geringen Verlust Luftkanäle Diagramm Druckabfall Fluss pa

## Search the Engineering ToolBox

- "the most efficient way to navigate!"

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your SketchUp model with the Engineering ToolBox - SketchUp Extension/Plugin - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

Translate the Engineering ToolBox!