# Air Change Rate

## Calculate air change rates - equations in imperial and SI units

Sponsored Links

### Air Change Rate - Imperial Units

Air change rate - air changes per hour - expressed in imperial Units

n = 60 q / V (1)

where

n = air changes per hour (1/h)

q = fresh air (make up air) flow through the room (Cubic Feet per Minute, cfm)

V = volume of the room (Cubic Feet)

### Air Change Rate - SI Units

Air change rate expressed in SI-units

n = 3600 q / V (2)

where

n = air changes per hour

q = fresh air (make up air) flow through the room (m^{3}/s)

V = volume of the room (m^{3})

### Example - Air Change Rate SI Units

With an air flow of *3 m ^{3}/s* in a

*20000 m*room the air change rate can be calculated as

^{3}

n = 3600 (3 m^{3}/s) / (20000 m^{3})

= 0.54 (h^{-1})

### Typical Air Changes per Hour

Typical air changes per hour for well-insulated spaces:

- no windows or exterior doors -
*0.33 (1/h)* - windows or exterior doors on one side -
*0.67 (1/h)* - windows or exterior doors on two sides -
*1 (1/h)* - window or exterior doors on three sides -
*1.33 (1/h)*

Sponsored Links

## Related Topics

Sponsored Links