# Chilled-Water System

## Chilled-water systems formulas - evaporator and condenser flow rates

Sponsored Links

In a chilled-water system the air conditioner cools water down to *40 - 45 ^{o}F (4 - 7^{o}C)*. The chilled water is distributed throughout the building in a piping system and connected to air condition cooling units wherever needed.

### Total Heat Removed

The total heat removed by air condition chilled-water installation can be expressed as

h = 500 q dt (1)

where

h = total heat removed (Btu/h)

q = water flow rate (gal/min)

dt = temperature difference (^{o}F)

### Evaporator Flow Rate

The evaporator water flow rate can be expressed as

q_{e}= h_{tons}24 / dt (2)

where

q_{e}= evaporator water flow rate (gal/min)

h_{tons}= air condition cooling load (tons)

### Condenser Flow Rate

The condenser water flow rate can be expressed as

q_{c}= h_{tons}30 / dt (3)

where

q_{c}= condenser water flow rate (gal/min)

h_{tons}= air condition cooling load, chiller tonnage(tons)

Sponsored Links

## Related Topics

## Related Documents

## Tag Search

- en: chilled water cooling load tons evaporator condenser