# Flow Rate Calculated with the Velocity-Area Principle

## Calculate flow rate or discharge in an open conduit, channel or river based on the velocity-area principle

The velocity-area principle is based on velocity measurements in a open flow like a conduit, channel or river.

Velocities and depths across the stream are measured as indicated in the figure above. A partial discharge in a section of the stream can be calculated as

qn = vn an              (1)

where

qn = flow rate or discharge in section n    (m3/s, ft3/s)

vn = measured velocity in section n   (m/s, ft/s)

an = area of section n   (m2, ft2

One simple way to express the section area is

an = dn (ln+1 - ln-1) / 2                              (2)

The total flow in the stream can be summarized to

Q = Σ1n vn an                         (3)

where

Q = summarized flow rate or discharge in the conduit   (m3/s, ft3/s)

The accuracy of estimate depends on the profile of the conduit and the number of measurements. For conduits with regular shapes like rectangular channels a limited number of measurements are required. For irregular shapes - like natural rivers or similar - higher accuracy requires more measurements both horizontal and vertical.

### Example - Computing Flow Rate in a Channel

From a conduit we have three measurements:

Measured ValuesCalculated Values
nv
(m/s)
d
(m)
l
(m)
a
(m2)
q
(m3/s)
0 0 0 0
1 3 1 2 2 6
2 4 1.5 4 3 12
3 3 0.9 6 1.8 5.4
4 0 0 8
Summarized 23.4

The section areas can be calculated like

a1 = (1 m) ((4 m) - (0 m)) / 2

= 2 m2

a2 = (1.5 m) ((6 m) - (2 m)) / 2

= 3 m2

a3 = (0.9 m) ((8 m) - (4 m)) / 2

= 1.8 m2

The flow rates can be calculated as

q1 = (3 m/s) (2 m2)

= 6 m3/s

q2 = (4 m/s) (3 m2)

= 12 m3/s

q3 = (3 m/s) (1.8 m2)

= 5.4 m3/s

The total flow can be summarized as

Q = (6 m3/s) + (12 m3/s) + (5.4 m3/s)

= 23.4 m3/s

Note - there are alternative ways to calculate the section flow rates:

### Simple Average Method

Using the simple average of two successive vertical depths, their mean velocity, and the distance between them can be expressed as

qn to n+1  = [(vn + vn+1) / 2] [(dn + dn+1 ) / 2] (ln+1 - ln)                  (4)

### Midsection Method

With the midsection method, the depth and mean velocity are measured for each number of verticals along the cross section. The depth at a vertical is multiplied by the width, which extends halfway to the preceding vertical and halfway to the following vertical, to develop a cross-sectional area. The section flow rate can be expressed as

qn = vn [((ln - ln-1) + (ln+1 - ln)) / 2] dn                 (5)

## Related Topics

• Flow Measurement - Flow metering principles - Orifice, Venturi, Flow Nozzles, Pitot Tubes, Target, Variable Area, Positive Displacement, Turbine, Vortex, Electromagnetic, Ultrasonic Doppler, Ultrasonic Time-of-travel, Mass Coriolis, Mass Thermal, Weir V-notch, Flume Parshall and Sluice Gate flow meters and more

## Related Documents

• Types of Fluid Flow Meters - An introduction to different types of fluid flowmeters - Orifices, Venturies, Nozzles, Rotameters, Pitot Tubes, Calorimetrics, Turbine, Vortex, Electromagnetic, Doppler, Ultrasonic, Thermal, Coriolis
• Weirs - Open Channel Flow Rate Measurement - Weirs can be used to measure flow rates in open channels and rivers - common for water supply and sewage plants
• Flowmeter Accuracy - Introduction to accuracy in flow measurement devices
• Measurement of Water Flow - A manual providing guidance in selecting, managing, inspecting, and maintaining water measurement devices - describes standard methods and devices commonly used to measure irrigation water
• Flow Units Converter - Convert between volume flow units - gpm, liter/sec, cfm, m3/h - an online flow unit calculator
• Comparing Flowmeters - A limited comparison of flowmeter principles - regarding service, rangeability, pressure loss, typical accuracy, upstream pipe diameters, viscosity and relative costs
• Orifice, Nozzle and Venturi Flow Rate Meters - The orifice, nozzle and venturi flow rate meters use the Bernoulli Equation to calculate fluid flow rate using pressure difference through obstructions in the flow
• U-Tube Manometer - The inclined and vertical u-tube manometers are inexpensive and common in the differential pressure measurement with flow meters like pitot tubes, orifices and nozzles
• Sluice Gate Flow Measurements - Sluice gates are used for controlling and measuring flow rates in open channels and rivers, mainly in connection to hydro power plants
• Flowmeters and Turndown Ratio - Rangeability - Turndown ratio for flow measurement devices like orifices, venturi meters etc.
• Hydrostatic Pressure - Depth and hydrostatic pressure

## Search the Engineering ToolBox

- "Search is the most efficient way to navigate the Engineering ToolBox!"

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your SketchUp model with the Engineering ToolBox - SketchUp Extension/Plugin - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!

Translate the Engineering ToolBox!